1 USER MANUAL On-Line UPS Model ZS VA/2000VA/3000VA Uninterruptible Power Supply System 1 2
2 1 Introducti 1. 1 Descripti of Commly Used Symbols Some or all of the following symbols may be used in this manual and may appear in your applicati process. Therefore, all users should read the form carefully and thoroughly. Symbol Symbol & Descripti Descripti Cauti, danger Danger electric shock Alternating current (AC) Direct current (DC) Protective ground Recycle Do not dispose with ordinary trash 1. 2 Safety Instructis 1. Read this manual carefully and thoroughly before operati the UPS and save this manual properly for future reference. 2. Do not tear up or shatter the alarm table the UPS and pay attenti to it. 3. Please do not overload the UPS. 4. The UPS ctains large capacity batteries. The case of the UPS must not be opened by untrained persnel. Otherwise, it may cause electric shock. 5. Do not short the positive and negative electrodes of battery. Otherwise, it may cause electric shock or fire. 6. Do not plunge or insert any objects into the air vents and other inlets. 7. Do not store or use the device in the following envirment: Where there is inflammable gas, corrosive agents or heavy dust Where the temperature is very high or low (above 40 or below 0 ) or the humidity is very high(more than 90%) Under direct sunlight or close to heating facilities Place of strg vibratis 8. In the event of fire occurring in the vicinity, please use dry powder fire extinguishers.the use of liquid fire extinguishing agents may cause electric shock. 3 4
3 2 Product Descripti 2. 2 The Appearance of the UPS The ST-series is an -line uninterruptible power supply device incorporating double-cverter technology with single-phase input and single-phase output. It offers the high quality power supply with the greatest degree of availability and reliability. The 1-3kVA of ST series is compact and cvenient for users, especially for the basic equipments in some areas such as: finance, communicati, government, traffic, manufacture, educati and so System Type and Cfigurati There are two types of UPS according to the battery cfigurati: standard type and lg backup time type, each available in the following ratings: 1kVA, 2kVA and 3kVA UPS. Table 2-1 UPS types and cfiguratis Figure 2-1 The rear panel of ZS110-1K-KS Type Model Remark 1kVA ZS110-1K With a 1A internal charger and 3 build-in batteries of 12V/ 7AH Standard 2kVA ZS110-2K With a 1A internal charger and 6 build-in batteries of 12V/ 7AH 3kVA ZS110-3K With a 1A internal charger and 8 build-in batteries of 12V/ 7AH 1kVAS ZS110- With a 7A internal charger and external battery slot. Lg Backup Time 2kVAS 3kVAS 1K-KS ZS110-2K-KS ZS110- With a 7A internal charger and external battery slot. With a 7A internal charger and external battery slot. Figure 2-3 The rear panel of ZS110-2K-KS-ZS110-3K * The picture for back panel is just for reference, it subjects to change customer s requirement, please refer to the real subject. 3K-KS Note: -KS model means Lg Backup Time. 5 Note:The appearances above are examples with the lg backup time, the correspding standard type is without the External Battery slot. 6
4 2. 3 Operating Principle the fault type, and the fault informati will be reported through the communicati ports. 6. Charger: The charger of standard UPS provides 1A charging current; and lg backup time provided 7A charging current. 7. Battery: Sealed maintenance-free lead acid battery can be used as the DC source of the UPS. 8. Output filter: It filters the output and provides clean AC power to the load. Figure 2-4 The UPS operating principle 1. Input filter: it filters the input and provides clean AC power to the UPS. 2. AC/DC cverter: In Normal mode, it cverts the AC input power to regulated DC power, and raises the regulated DC voltage for DC/AC cverter. 3. DC/DC cverter: Raises the DC Voltage from the battery system to the optimum operating voltage for the inverter when the UPS operates in Battery mode. 4. DC/AC inverter: In Normal mode, it utilizes the DC output of the AC/DC cverter and inverts it into precise, regulated sine wave AC power. In Battery mode, it receives energy from the battery through the DC/DC cverter. 2 Product Descripti 5. Bypass: It is very important in the UPS system. In the event of a UPS fault that will not lead to UPS shutdown, the load will be automatically transferred to the bypass. Meanwhile, the LED indicators will indicate 7 8
5 3 Installati 3. 1 Unpacking Inspecti 1. Open the packing box of UPS and take it out, visually examine the unit for transit damage. 2. Check against the accessory lists that the accessories of the UPS are present. (Refer to Table 9-1). 3. Make sure the model is what you wanted from the nameplate the rear panel 4. If the UPS arrives damaged, or there is any missing accessory or other questi above, please ctact the distributor immediately Cable Cnecti Cnecting Input and Output Cables 1. Input cable cnecti If the UPS is cnected via the power cable, please use a proper socket with over current protecti, and pay attenti to the capacity of the socket: over 10A for ZS110-1K(-KS), over 16A for ZS110-2K(-KS) and ZS110-3K(-KS). A side of input wiring has been fixed with the UPS, and the other side is just need to plug into the input socket. The wiring cfigurati is shown in the following diagram Installati Notes 1. When locating the UPS, make sure there is no hazardous objects such as water, inflammable gas, corrosive agents and so around the UPS, and that the installati envirment meets the specificatis. 2. The UPS should not be placed a side. The air inlet port at the frt panel and the outlet port the rear panel and two side panels should not be blocked so as to ensure good ventilati. 3. In case if the UPS is unpacked, installed and used at very low temperatures, cdensatis of water drops may appear. It is necessary to wait until the UPS fully dried inside out before proceeding to installati and use. Otherwise, they may be a risk of electric shock. 4. Place the UPS near the utility power source outlet which supplies power to the UPS. In any emergency, switch off the main input socket, cut off the battery voltage input. All power sockets must be cnected with ground protecti. Figure 3-1 Cnecti Method of Input 2. Output cable cnecti The output of ZS110-1K(-KS)/ ZS110-2K(-KS)/ ZS110-3K(-KS) all available to uses sockets. The total output power shall not exceed 1kVA/0.8kW, 2kVA/1.6 kw,3kva/2.4 kw. Simply plug the load power cable to the output sockets of UPS to complete cnecti as shown in the following diagram. 9 10
6 Figure 3-2 Cnecti method of output Operati Procedure of External Battery for Lg Backup Time UPS The battery cnecti procedure is very important for lg backup model. Any incompliance may result in the risk of electric shock. Therefore, the following steps must be strictly complied with. 1. First cnect in series the batteries of the pack to ensure proper battery voltage that ZS110-1KS for 36VDC, ZS110-2KS for 72VDC, ZS110-3KS for 96VDC. 2. Take out the battery cable delivered with the UPS, e end of the external battery cable is a plug for cnecting the UPS, the other end has 3 open wires for cnecting the battery pack. 3. Cnect the external battery cable to the battery terminal (DO NOT cnect the battery socket of the UPS first. Otherwise, it may cause electric shock). Cnect the red wire to the + terminal of the battery. The black wire is cnected to the - terminal of the battery. The green/yellow wire is grounded for protecti purpose. 4. Cnect the plug of the external battery cable to the external battery slot the rear panel of the UPS to complete the cnecti procedure. Figure 3-3 Battery cnecti diagram for Lg Backup time models Note: The length of the external battery cable is 1.6 m, If users need a lger e, please csult the distributor. There is a limit to the length of the external battery cable to ensure normal operati of the UPS Cnecting Communicati Cable 1. Computer interface 11 12
7 Computer interface: The type of signals is provided by the UPS to communicate with a host computer through communicati cable included in the standard accessory, User can use special mitor software UPSil in the standard accessory to mitor the UPS through the port. 4 Chapter Empty, not present any more 2. Alternative cnecti of communicati Intelligent Slot: It is designed for installing the dry ctact card, SNMP card and 485 card. You can choose for e of them to installed a-dry ctact card: You can utilize mitor functi of dry ctact to manage the power supply directly. b-snmp: It enables you mitor the UPS remotely through Internet. c -485: Central mitor card. Note: Please remove the cover board of the intelligent slot before any card is installed
8 5 Operati (LCD model) 5.1 Operati Display Panel c) LCD display screen switch Pressing the functi butt for more than 1 s and less than 2 s (buzzer beeps ce) to switch LCD display screen 4 LED indicators The LED indicators ctains, Bypass indicator, utility power indicator, Inverter indicator, Battery indicator. The definiti of each indicator is the same as LED panel (refer to table 4-1). 5.2 Operati Mode 1. ON butt: Pressing the ON butt more than 1 (buzzer beeps ce), the UPS system is turned. 2. OFF butt: By pressing this butt more than 1 (buzzer beeps ce) turns off the UPS system whenever the UPS run under the normal mode/battery mode. 3. Functi butt The Functi butt provides the following functis: a) Battery self- diagnosis: When the UPS ran in normal mode, pressing this butt more than 2 s (buzzer beeps twice) can start the battery self-diagnosis. b) Silence functi in battery/bypass mode In battery/bypass mode, when the buzzer beeps, pressing and holding the functi butt for more than 2 s (buzzer beeps two times) can silence the buzzer. Press the butt for more than 2 s (buzzer beeps twice) again to resume the alarm functi 15 UPS Operati Mode ctains normal mode, battery mode and bypass mode. Under the three modes, the page showing output voltage and output frequency is the main display page. If users need more informati about UPS, Pressing the functi butt can initiate display screen switch. If the current page is not the main page, UPS will automatically switch back the main page after 30 s. In order to extend the LCD usage life, the backlight will turn off after 1 minute without any switch operati. At this point, Users just need to touch any butt briefly to turn the backlight Normal mode When operating in the normal mode, the display of main page the frt panel is shown as the figure 5-2. The utility power indicator and the Inverter indicator are turned. Load informati area shows load value, and the battery level area indicates dynamically when the battery is not fully charged (the battery level ics lit e after another circularly). When the battery is fully charged, all the level ics are turned. 1) If the utility power indicator blinks, it indicates that there are problems with reversed polarity (L, N) of site wiring or discnect with ground. UPS is still working in normal mode. If the battery indicator is turned at the same time, it shows that the voltage or frequency of the utility power is out of the normal input range of the UPS. The UPS works in battery mode. 16
9 5.2.2 Battery Mode When operating in the battery mode, the display of main page the frt panel is shown as the figure 5-3. The battery indicator and the Inverter indicator are turned. If the utility power indicator blinks at the same time, it shows that the utility power is abnormal. Load informati area shows load value, and bat level area shows current battery capacity. Figure 5-2 Normal Mode 2) If load is more than 100 percent, the buzzer beeps, meanwhile, the warning ic blinks too, reminding that UPS is overloaded. You should get rid of some unnecessary loads e by e to decrease the loads until the alarm clear 3) If the battery indicator blinks, it indicates that no battery is cnected to the UPS or battery voltage is too low. You should check if battery is properly cnected to the UPS, and press functi butt more than 2 s to start the battery self-diagnosis. If the cnecti between battery and UPS is cfirmed without any problem, it may be due to the defect or aging of the battery, please refer to the troubleshooting in chapter 7 to solve the problem accordingly. 4) The other four display pages are load percent page, actual load page, input informati page and the maximum temperature page. Note:Cnecti to a power generator has to be made according to the following: Activate the power generator and wait until the operati is stable before cnecting the output of the power generator to the UPS (be sure that the UPS is in idle mode). Then, turn the UPS according to the startup procedure. After the UPS is turned, the loads are cnected e by e. It recommended that the capacity of the generator should double than UPS. 17 1) When the UPS is running in battery mode, the alarm will beep 4 s. If the Functi key is pressed for more than 2 s, the alarm will not beep (silence functi). Press the Functi key more than 2 s again to resume the alarm functi. Figure 5-3 Battery Mode 2) When the battery capacity decreases, the number of battery capacity indicators turned will decrease. If the battery voltage drops to the pre-alarm level, the alarm will beep to remind the user of insufficient battery capacity. 3) The other four display pages are load percent page, actual load page, battery informati page and the maximum temperature page Bypass Mode When operating in bypass mode set up through UPSil software, the display the frt panel is shown as the figure 5-4, the utility power indicator and the bypass indicator are turned. Load informati area shows load value, and the battery level area indicates dynamically when the 18
10 battery is not fully charged (the battery level ics lit e after another circularly). When the battery is fully charged, all the level ics are turned. 1) When operating in bypass mode, the UPS beeps 2 minutes. If the Functi key is pressed for more than 2 s, the alarm will not beep (silence functi). Press the Functi key more than 2 s again to resume the alarm functi. 2) If the utility power indicator blinks, it shows that the voltage or frequency of the utility power is out of the input range of the UPS or there are problems with reversed polarity (L/N) of site wiring or discnect to the ground for protecti. 3) The other four display pages are load percent page, actual load page, input informati page and the maximum temperature page. Notes: When operating in bypass mode, the backup functi of the UPS is not available and the power used by the load is directly from the utility power via internal EMI filter. Figure 5-5 Fault display When a warning occurred, the fault ic blinks, and users can switch to the alarm display page shown as the figure 5-6 to check the warning code. Figure 5-6 Alarm display Figure 5-4 Bypass Mode LCD indicati of UPS alarm status and faults In the event of an UPS fault, UPS enters fault operati mode, at this point, the fault ic turns csistently, the buzzer beeps and the data informati area shows current fault code (refer to table 6-2), the display the frt panel is shown as the figure 5-5, users can switch to output page by pressing functi butt
11 5.3 Operating Instructis UPS ON/OFF Operati Note: The battery is fully charged before delivery. However, storage and transportati will inevitably cause some charge loss. Therefore, it is advisable to charge the battery for 10 hours before using it, so as to ensure adequate battery capacity. 1. Turning the UPS The operati of turning the UPS ctains: turning with utility power and turning without utility power. 1) Turning with utility power: Cnect the mains input to the UPS, press the ON butt more than e, UPS starts to turn. At this point, the LCD begins to cduct self-diagnosis (all the LCD indicators are turn about 4 s). A few s later, the UPS will begin to operate in Normal mode; meanwhile, the utility power indicator, inverter indicators will turn. If the utility power is abnormal, the UPS will work in battery mode. 2) Turning without utility power: With no mains input feed to the UPS, press the ON butt more than e, ups start to turn, At this point, the LCD begins to cduct self-diagnosis (all the LCD indicators are turn about 4 s). A few s later, the battery indicator, inverter indicators will be turn to indicate that the UPS is working in battery mode. 3). Powering down the UPS The operati of powering down the UPS ctains: turning off ups in normal mode, turning off ups in battery mode 4) Completely power down the UPS from Normal mode Hold and press the OFF butt persistently for more than 1 to 21 power off the UPS. If it bas been set up to work in bypass mode by software, the bypass indicator will be turned to indicate that the UPS is working in bypass mode. In order to cut off the output from the UPS, simply cut off the utility power supply. LCD begins to cduct self-diagnosis (all the LCD indicators are turned about 4 s),a few s later, not any display is shown the frt panel and no output is available from the UPS outlets, system completely power down. 5) Completely power down the UPS from Battery mode Press the OFF butt persistently for more than 1 to power off the UPS. When being powered off, the LCD will start self-diagnosis (all the LCD indicators are turn about 4 s), a few s later, not any display is shown the frt panel and no voltage output is available from the UPS outlets, system completely power down Cducting Battery self-diagnosis In UPS operati, users can manually initiate battery self-diagnosis to check the battery cditis. There are two methods to initiate the battery self-diagnosis: 1. Through the functi butt In normal mode, press and hold the functi for more than 2 s until the buzzer beeps twice. At this point the indicators (LED7~10) will blink cyclically, indicating the UPS has worked in battery mode and the battery self-diagnosis has started. The battery self-diagnosis will last for 10 s default. In the event of a battery fault during battery self-diagnosis, the UPS will transfer to normal mode automatically. 2. Through the mitor software Users can also initiate battery self-diagnosis through the background mitoring software. 22
12 6 Maintenance 6.1 Battery Maintenance The battery is key compent of the UPS. The battery life depends the ambient temperature, charging and discharging times. High ambient temperature and deep discharging will shorten the battery life. 1. Sealed maintenance-free lead acid battery be used in the standard. When being cnected to the utility power whether the UPS has been turned or not, the UPS keeps charging the battery and also offers the protective functi of charging and discharging. 2. Keep the ambient temperature between 15 and If the UPS has not been used for a lg period, charging is recommended at the intervals 3 mths. 4. Batteries should not be replaced individually. 5. Under normal cditis, the battery life lasts 3 to 5 years. In case if the battery is found not in good cditi, earlier replacement should be made. The battery should ly be replaced by qualified service persnel Checking UPS functi Every time when cducting field maintenance, please check the regular functi of the UPS, including: 1. Check the operati status of the UPS If the main voltage is within the specificatis, the UPS should operate in normal mode; if the main voltage is abnormal, the UPS should operate in battery mode. In both cases, there should be no fault indicati. 2. Check the transfer between the UPS operati modes Discnect the main input to simulate a mains failure, the UPS should transfer to battery mode and operate normally; then recover the mains input, the UPS should transfer to normal mode and operate normally 3. Check the LED indicators of the UPS During the check processes stated above, check that the LED indicati of the UPS agrees with the UPS operati mode. Note: 1.Prior to battery replacement, the UPS must be turned off and discnected from utility power. 2. Metal objects such as rings and watches should be removed. 3. Use the screwdriver with insulated handle. Tools and other metal objects should not be placed the battery. 4. Short circuit or reverse cnecti between the positive and negative terminal of the battery is strictly forbidden
13 7 Troubleshooting In the event of an UPS fault, shoot the trouble according to Table 6-1. If the fault still persists, please ctact our customer service center. Fault/Warning code F01 F02 F03 F04 F05 F06 F07 F08 F09 A01 Faults Fault ic Blink ce Alarm ce 25 Possible cause Internal fault. Internal fault. Internal fault. The UPS output is short circuited Internal fault. Internal fault. Overload fault Internal overheat The charger of the UPS is defective Overload pre-warning Soluti Please ctact the distributor or Service center Please ctact the distributor or Service center Please ctact the distributor or Service center Turn off the UPS. Remove all loads. Ensure that the loads are not failed or the UPS has no internal short before turn it again. If failed, please ctact the distributor or service center Please ctact the distributor or Service center Please ctact the distributor or Service center Reduce the member of loads cnected to the UPS. Ensure that the UPS is not overloaded and the ventilati opening is not blocked and ambient temperature is not too high. Wait for 10 min. for the UPS to cool down before turning it again. If it does not work. Please ctact the distributor or service center. Please ctact the distributor or Service center Reduce the member of loads cnected to the UPS. 7 Troubleshooting Fault/Warning code A02 A03 A04 A05 A06 Faults Fault ic Blink ce Blink ce Blink ce Blink ce Blink ce Alarm ce ce ce ce two minutes 26 Possible cause Battery overcharging UPS power abnormal Battery voltage low Fan failure Maybe reversed polarity (L,N) of site wiring or discnect with ground. Soluti Please ctact the distributor or Service center Check the battery of the UPS cnected properly. The UPS output will be cut off, please switch to the backup power. Ensure that the fan is not locked Please check the polarity of the neutral wiring and the line wiring, ensure that The green/yellow wire cnect protective ground properly Table 7-2 UPS troubleshooting of LCD panel indicator When you ctact the service center, please provide the following informati: Model No and Serial No of the UPS. The date when the problem arose. Complete descripti of the problem, including the panel display, alarm warning, and power cditi and the load capacity. If the UPS is a lg backup time model, you may also provide the battery informati.
14 8 Specificatis 8. 1 Electrical Input Output Battery Model ZS11 0-1K 1K-KS 27 ZS11 0-2K 2K-KS ZS11 0-3K ZS110- ZS110- ZS110-3K-KS Rating 1KVA/800W 2KVA/1600W 3KVA/2400W Input system Rated voltage Voltage range Frequency Single phase & earth ground 220VAC 115VAC~300VAC 50Hz Power factor 0.99 Voltage range of bypass Output system Rated voltage (80±5)VAC~(286±5)VAC Single phase & earth ground 220VAC Power factor 0.8 Voltage precisi ±2% Output frequency Normal mode Battery mode Inverter overload capacity(utility power,25 ) Transfer time 1.The output frequency synchrizes with the input frequency when the input frequency is in the range of 46 Hz~54 Hz 2.The output frequency is 50Hz when the input frequency is not in the range of 46 Hz~54 Hz 105%±5%<Load 125%±5% 50s transfer to bypass 125%±5%< Load <150%±5% 25s transfer to bypass Load > 150%±5%,300ms transfer to bypass 0ms (Normal mode Battery mode) <4ms(Normal mode Bypass mode) Crest factor 3:1 Batteries voltage 36VDC 72VDC 96VDC Battery Quantity 3 ne 6 ne 8 ne Battery Type Backup Time(25 ) Sealed maintenance-free lead acid battery of battery voltage 12V/7AH Full load 5min (Standard) Charge current 1A 7A 1A 7A 1A 7A 8. 2 Mechanical Model W*H*D(mm) Weight(kg) ZS110-1K ZS110-2K ZS110-3K ZS110-1K-KS ZS110-2K-KS ZS110-3K-KS Envirmental Item Ambient temperature Envirment humidity Altitude Storage temperature 28 Normal range 0 ~40 20%~90%(No cdensati) Lower than 1000m: no derating Over 1000m :1% derating for 100m rise -15 ~ EMC Item Standard Level ESD IEC LEVEL4 RS IEC LEVEL3 EFT IEC LEVEL4 Surge IEC LEVEL Safety Comply with GB , IEC and CE requirements Industry Standard Comply with EN62040,YD/T requirements.
15 9 Appendix 9.1 Csignment Lists Model Type Accessories No Machine 1 Standard Model Intelligent mitor software CD 1 User Manual 1 Lg backup time Model Serial communicati cable 1 Machine 1 Intelligent mitor software CD 1 User Manual 1 External Battery Cable 1 Serial communicati cable 1 29
On Line UPS LUC 1000E / LUC 2000E / LUC 3000E User Manual Save This Manual Please read this manual carefully prior to storage, installation, wiring, operation and maintenance of the UPS. This manual contains
System Sump and Pump VICTRON MULTIPLUS COMPACT 12/800/35 & 12/1200/50 - Advanced Battery Backup System Operatial Manual Rev 2.2-10 October 2017 Newt Waterproofing Systems INTRODUCTION CONTENTS The Victr
Manual EN Appendix MultiPlus (firmware xxxx1xx) 12 3000 120-50 120V 24 3000 70-50 120V 1. SAFETY INSTRUCTIONS In general Please read the documentati supplied with this product first, so that you are familiar
User Manual 3/1 10K/20K Online UPS with Isolation Transformer Uninterruptible Power Supply System Please comply with all warnings and operating instructions in this manual strictly. Save this manual properly
Power Inverter Diamond Series CPD1200EILCD User s Manual 2 TABLE OF CONTENTS 1 IMPORTANT SAFETY INSTRUCTIONS..4 2 INSTALLATION....5 2-1 Unpacking...5 2-2 Product Overview & Outlook..5 2-3 Power Requirements
THIS MANUAL CONTAINS IMPORTANT SAFETY INSTRUCTIONS, KEEP THIS MANUAL HANDY FOR FUTURE REFERENCE. INSTALLATION AND OPERATION Before installation, please read and understand the following instructions: Inspect
Pure Sine Wave Inverter Charger Renogy 1000W 2000W Pure Sine Wave Inverter Charger Manual 2775 E. Philadelphia St., Ontario, CA 91761 1-800-330-8678 Version 1.6 1 Important Safety Instructions Please save
USERS- AND INSTALLATION MANUAL Mass Sine 24/10000 Mass Sine 24/15000 Modular high power inverter system MASTERVOLT Snijdersbergweg 93, 1105 AN Amsterdam The Netherlands ENGLISH: PAGE 1 Tel.: +31-20-342
Sola 3000 Guide Specifications CSI 16610 - Static Uninterruptible Power Supply Systems - Sola 3000 Guide Specifications for a 700 to 2200 VA Single - Phase Uninterruptible Power Supply System 1.0 GENERAL
p/n 88-020292-01 A Automati E-AC Drive Hardware Installati Guide Effective: April 9, 2002 User Informati WARNING!! E Series products are used to ctrol electrical and mechanical compents of moti ctrol systems.
For more information, visit www.247technology.com/single-phaserackmounttower-ups/xtreme-power-conversion-xprt-6-10 XPRT 6kVA & 10kVA Online UPS 6kVA, 10kVA Models User & Installation Manual 2015. All rights
Operating Instructions for Your Cobra 150 Watt INVERTER M ODEL CPI 150 Nothing comes close to a Cobra 00 Congratulations Thank you for purchasing the CPI 150 Power Inverter from Cobra. When used properly,
Back-UPS CS Back-UPS CS 350 APC Back-UPS CS, 210 Watts / 350 VA,Input 120V / Output 120V, Interface Port DB-9 RS-232, USB Includes: CD with software, Cord management straps, USB cable, User Manual Standard
TACOMA 3/1 SERIES 10KVA ~ 20KVA On-Line UPS USER MANUAL Maruson Technology Corporation 18557 East Gale Avenue City of Industry, California 91748, U.S.A. Tel: +1-626-912-8388 Fax: +1-626-912-8680 Toll Free:
User Manual Easy UPS On-Line SRV Series 1000VA, 2000VA, 3000VA Important Safety Information Read the instructions carefully and look at the equipment to become familiar with the device before trying to
Industrial On-Line UPS - 120 V, 700 VA - 3000 VA S4KC Series Instruction Manual While every precaution has been taken to ensure accuracy and completeness in this manual, Appleton Grp LLC d/b/a Appleton
Återförsäljare: Tre Röda AB TillingeHagby 7-745 94 ENKÖPING Tel: 08-560 200 22 e-post: email@example.com http: www.treroda.nu When the INSIDE is important make the OUTSIDE Cannon TECHNICAL DATA SHEET 400-500-600-800
NXTi Online Three-Phase UPS 3P-3P: 20kVA, 30kVA Models USER & INSTALLATION MANUAL www.xpcc.com 2013 Xtreme Power Conversion Corporation. All rights reserved. Please comply with all warnings and operating
PowerSure TM Personal XT 450, 700, 1250 VA 230V USER MANUAL English / Deutsch / Français / Italiano / Español IMPORTANT SAFETY INSTRUCTIONS SAVE THESE INSTRUCTIONS This manual contains important safety
Pure Sine Wave Inverter GP-HS1500 Owner s Manual 2 Table of Contents Introduction 3 Specifications 4 Name and Main Function 5 Installation 7 Operation 9 Operating Limits 13 Troubleshooting 13 Maintenance
Digit al Energy T M L P Seri es Di gi ta l Energy TM LP Series Digita l Energ y T M L P Se rie s GE Consumer & Industrial Power Protection Technical Data Sheets Digital Energy Uninterruptible Power Supply
065A 0 Vac to 0/0 Vac Conversion Kit For Electronic Air Cleaners Application The 065A Conversion Kit changes the 0 Vac, 60 Hz to 0/0 Vac, 50/60 Hz. The kit includes a transformer and two screws. The line
Growatt 10000HY Installation & Operation Manual GROWATT NEW ENERGY TECHNOLOGY Co.,LTD No.28 Guangming Road, Shiyan, Baoan District, Shenzhen, P.R. China T F E W + 86 755 2747 1900 + 86 755 2747 2131 firstname.lastname@example.org
GSL Electronics Modified Sine Wave Power Inverters Congratulations on choosing one of our Modified Sine Wave Inverters for your application. There are 6 models in the range, which will meet most of your
08, 08 Replacement Power Supply Kit for Electronic Air Cleaner APPLICATI INSTALLATI INSTRUCTIS These kits replace the power supplies with W8600E solidstate performance indicators (SSPI) used in the F0F
V Series 120/120VAC Standard 1000VA, 2000VA & 3000VA Universal Tower/Rack Mount LB Extended Models 900VA, 1700VA & 2500VA On-line, Single Phase, Double Conversion UPS The UniStar V features a field-proven
V Series 120/120VAC Universal Tower/Rack Mount Standard 1000VA, 1500VA, 2000VA & 3000VA LB Extended Models 900VA, 1250VA, 1700VA & 2500VA On-line, Single Phase, Double Conversion UPS The UniStar V features
Version 1.1 Version 2 Nature Power Inverters True Sinewave Inverter Modified Sinewave Inverter Owner s Manual!!!!!!!!!!! 38304 38204 For safe and optimum performance, the Power Inverter must be used properly.
PowerScale TECHNICAL SPECIFICATIONS PowerScale highlights at a glance Best in class efficiency Cost savings during the entire life-cycle(tco) Low input harmonic distortion Cost saving during installation
User Manual English APC Smart-UPS 750/1000/1500 VA 100/120/230 Vac 2U Rack-Mount Uninterruptible Power Supply 990-1194D 03/2012 Introduction The APC Uninterruptible Power Supply (UPS) is designed to prevent
R90 Online UPS 20kVA Model User & Installation Manual www.xpcc.com 2015. All rights reserved. (Rev 8/19/15) Table of Contents Introduction...6 Product Description... 6 Main Features...6 System Configuration...7
www.mgeups.com _ Evolution 650/650 Rack U 850/850 Rack U 50/50 Rack U 550/550 Rack U Installation and user manual P O W E R P R O V I D E R R U P T I B L E T E R N I N E U T H 3400364FR/AA - Page 3400835EN/AA
48-3000RM 2U 19, 2 Post Rack Mount & 4 Post Open Frame Cabinet Mount Pure Sine Wave Inverter User Manual Newmar PO Box 1306 Newport Beach, CA 92663 www.poweringthenetwork.com Tel: 714-751-0488 M-483000RM
Go Power! Manual GP-1000 Inverter Go Power! Electric Inc. PO Box 6033 Victoria, BC V8P 5L4 Tel: 866-247-6527 Fax: 866-607-6527 Email: email@example.com Table of Contents 1. INTRODUCTION 3 2. SPECIFICATIONS
Solar Inverter Manual Introduction SMPS series solar inverter power charging efficiency increased by 30%~60% than traditional controller charging. This inverter has automatic identification, three-stage
DC TO AC POWER INVERTER 12V / 24V / 48Vdc Input 115V / 230Vac Output 150W ~ 6000W Output cont. L-Series User Manual Before install and use your Inverter, read the User Manual and safety instructions. Cooler
ENGLISH Installation and user manual Tower models 5P 750 5P 1000 5P 1500 5P 850G 5P 1550G 1U Rack models 5P 550 R 5P 750 R 5P 1000 R 5P 1500 R 5P 850G R 5P 1550G R Copyright 01 EATON All rights reserved.
User Manual Smart-UPS On-Line SRC1KI-IN, SRC1KUXI Important Safety Information Read the instructions carefully to become familiar with the equipment before trying to install, operate, service or maintain
GE Consumer & Industrial Power Protection Operating Manual Uninterruptible Power supply Digital Energy LP 31 Series 8 10 15 20 kva 400 VAC CE / Series 1 GE imagination at work Model: LP 31 Series / 8 10
Pure Sine Wave DC TO AC Power Inverter User s Manual Distributed by: Tech Brands by Electus Distribution 320 Victoria Road, Rydalmere NSW Australia Tel: 1300 738 555 Fax: 1300 738 500 www.techbrands.com
Go Power! Manual GP-1750HD Inverter GP-2500 Inverter Go Power! Electric Inc. PO Box 6033 Victoria, BC V8P 5L4 Tel: 866-247-6527 Fax: 866-607-6527 Email: firstname.lastname@example.org Table of Contents 1. INTRODUCTION...
Back-UPS ES APC Back-UPS ES, 6 outlet 350VA, 120V, without auto shutdown software APC's Back-UPS ES series is now "greener" than ever. The ES 350 utilizes an ultra-efficient design that consumes less power
S150,S300 Series Pure Sine Wave Inverter User s Manual List of contents 1. Important Safety Instructions 3 1-1 General Safety Precautions 3 1-2 Precautions When Working With Batteries.. 3 2. Features...
Battery Power Inverters Renogy 500W 1000W 2000W Pure Sine Wave Inverter Manual 2775 E. Philadelphia St., Ontario, CA 91761 1-800-330-8678 1 Version 1.4 Important Safety Instructions Please save these instructions.
Operation Manual English APC Smart-UPS 1400 VA 3U Rack and Stack Uninterruptible Power Supply 230 Vac 990-1049, Revision 1 12/00 1: OPERATION INDICATORS AND CONTROLS ON THE SMART-UPS The APC Uninterruptible
Battery Charger Series EASY Charger User s manual 1 Warranty RIPEnergy is not manufacturer of these units. All technical information s, data s and dimensions rely on information s given by the manufacturer.
High-presicion Torque Meter Instruction Manual Applicable Models: AP-2, AP-10, AP-50, AP-100, AP-300 Thank you for purchasing the CHP Assembly Tool. In order to ensure maximum performance and product life,
ENGLISH 5P 1500 RT 5P 2200 RT 5P 2200 5P 3000 RT 5P 3000 Installation and user manual Copyright 2012 EATON All rights reserved. Service and suort: Call your local service representative Page 2 IMPORTANT
TECHNICAL SPECIFICATIONS OF 2 KVA POWER CONDITIONING UNIT 1.0 PURPOSE: 1. To charge the battery bank through Solar PV source and AC supply. 2. To invert and produce utility quality sine wave. 3. Inverters
A Complete solution for small battery-backed dc instrument power systems. DATASHEET Supply 12Vdc 8A or 24Vdc 6A loads Ideal for RTU s, dataloggers, remote field instrumentation, alarm systems, etc. where
Diesel Generator Set S3.8 Series Engine > Specification Sheet 44 kva 66 kva 50Hz 40 kw 60 kw 60Hz Description This Cummins Power Generation commercial generator set is a fully integrated power generation
1RECHARGEABLE APPLIANCES 1 CAUTION Certain rechargers for small nickel cadmium batteries can be damaged if connected to the unit. Two types of equipment are particularly prone to this problem: 1. Small
AUTOMOTIVE POWER INVERTERS INSTRUCTIONS Item #31463, #31464, #31465 EASTWOOD AUTOMOTIVE POWER INVERTERS are heavy-duty professional grade pieces of equipment designed to bring 120 volt power to any automobile.
PR1000ELCD / PR1500ELCD User s Manual K01-0000235-00 IMPORTANT SAFETY INSTRUCTIONS This manual contains important safety instructions. Please read and follow all instructions carefully during installation
FN Series Scalable N+ UPS kva to kva Rackmount Advanced Features: * Parallel Rackmount Units with a Single of up to kva * True N+ Redundancy * ECO Mode: 97% Efficiency * DSP Double-Conversion On-line Sinewave
S600,S600R Series Pure Sine Wave Inverter User s Manual Table of contents 1. Important Safety Information. 1 1-1 General Safety Precautions 1 1-2 Batteries Precautions.. 1 2. Features... 2 2-1 Applications..
Based on Statron s leading A.T.I.S. (Advanced Technology Industrial System) platform, the S3000 range is a true-industrial UPS system using the latest Power Factor Corrected (PFC) IGBT rectifier technology.
Fridge / Freezer / Warmer with DIGITAL TEMPERATURE CONTROL MODEL MHD13F-DM SPECIFICATION DESIGNATION OF PARTS MODEL CAPACITY OUTER DIMENSIONS INPUT RATING ( or FREEZER) (WARMER) REFRIGERANT WEIGHT MHD13F-DM
Activator 282 Aircraft Battery Maintenance Charger Operator Manual Revision 2.1a February 2013 This Operator Manual applies to the Activator 282 with a Liquid Crystal Display starting with Serial Number
1000-Watt Energy Center OPERATING INSTRUCTIONS Patent Pending Sierra Wave 1000-Watt Energy Center #9675 The Sierra Wave 1000-Watt Energy Center is a heavy duty and efficient portable power center offering