1 HX 3000 TB UK GENERATING SET USER AND MAINTENANCE MANUAL _0_1
2 A A A /4
3 A B C D /4
4 E F G 4/4
5 1. Preface 2. General description 3. Preparation before starting 4. Using the generator set 5. Safety features (if fitted, see specifications table) 6. Maintenance schedule Contents 7. Maintenance procedures 8. Storing the generating set 9. Fault finding 10. Specifications 11. Cable sizes 12. EC Declaration of conformity 1. Preface 1.1. Recommendations Thank you for buying one of our generating sets. We recommend that you read this manual carefully and follow the safety and maintenance advice and user instructions for your generating set very closely. The information contained in this manual is taken from technical data available at the time of print. In the intention of permanently improving the quality of our products, this information may be amended without warning Pictograms and plates on the generating sets and what they mean Warning: risk of electric shock Warning: the generating set is supplied without oil. Always check the oil level before starting the generating set. Earth, risk of burns A = Generating set model B = Generating set output C = Voltage D = Amperage E = Current frequency F = Power factor Important: refer to the documentation accompanying the generating set. 2 - Warning: emission of toxic exhaust gases. Do not use in a confined or poorly ventilated area. 3 - Stop the motor before filling with fuel. G = Protection rating H = Generating set noise output I = Generating set earth J = Reference Standard K = Serial number 1.3. Instructions and safety regulations Example of an identification plate Do not run the generating set without having put back the protective covers and closed the access doors. Never take the protective covers off or open the access doors if the generating set is running Warnings You are likely to encounter several warning symbols in this manual. This symbol indicates a definite risk to the health and life of people. Not following this instruction may seriously affect the health of people or prove fatal. Warning This symbol draws attention to the potential risk to the health and life of people. Not following this instruction may seriously affect the health of people or prove fatal _0_1
6 Warning This symbol indicates a dangerous situation if the warning is not heeded. Not following this instruction could result in non-serious injury or damage General advice One of the fundamental safety considerations is observation of the interval between maintenance procedures (see maintenance schedule). Furthermore, never attempt to carry out repairs or maintenance procedures without the necessary experience and/or tools. When you take delivery of your generating set, check that it is complete and not damaged in any way. A generating set should be handled gently, avoiding sudden movements, and the place where it is to be stored or used should be carefully prepared beforehand. Before use, it is essential that you know how to stop the generating set immediately and that you thoroughly understand all the controls and operations. Warning Never let other people use the generating set without giving them all necessary instructions beforehand. Never let children touch the generating set, even when it is not in operation. Do not operate the generating set near animals (as it could cause them to panic). Never start the motor without an air filter or exhaust. Never invert the positive and negative battery terminals (if fitted) when connecting them. Such an inversion can lead to severe damage to the electrical equipment. Never cover the generating set with any type of material while it is in operation or just after it has been turned off. Wait until the motor is cold. Never coat the generating set with oil in an attempt to protect it from corrosion. Some preservative oils are flammable. Also, some are dangerous to inhale. In all cases, respect the local regulations currently in place concerning the use of generating sets Safety guidelines to prevent electrocution While they are in operation, generating sets produce electric current. Connect the generating set to earth each time you use it, in order to prevent electrocution. Never touch stripped cables or disconnected connectors. Never handle a generating set with wet hands or feet. Never expose the equipment to liquid splashes or rainfall, and do not place it on wet ground. Always keep the electrical cables and the connections in good condition. Do not use equipment in a poor state of repair which could lead to electrocution or damage to the equipment. Use a differential protection device between the generating set and the appliances if the cable or cables used are more than 1 metre in length. This device must be positioned at a maximum distance of 1 metre from the generating set electrical sockets. Use flexible, durable cables, with rubber sheathing, conforming to the IEC standard or equivalent cables. Do not connect the generating set to other power sources, such as the mains. In specific cases where there is provision for a reserve connection to existing electrical networks, this must only be carried out by a qualified electrician, who should take the operating differences of the equipment into account, according to whether the public distribution network or generating set is being used. Special circuit breakers designed for use with generating sets are used to prevent electrocution. If these circuit breakers need to be replaced, circuit breakers with identical nominal ratings and specifications must be used Safety guidelines to prevent fire Keep all inflammable materials (e.g.: petrol, oil, fabric etc.) out of the way when the generating set is in operation. The motor should not be operated in areas containing explosive products. There is a risk of sparks forming where all electrical and mechanical components are not shielded. Never cover the generating set with any materials while it is operating or just after it has been switched off (wait for the motor cool down) Safety guidelines for exhaust gases Exhaust gases contain carbon monoxide, which is a highly toxic substance. This substance can cause death if it is present in excessive concentrations in the air inhaled. For this reason, always use the generating set in a well ventilated area, where gases will not be able to accumulate. Good ventilation is required for your generating set to work properly. Without this, the motor would very quickly run at too high a temperature, which could lead to accidents or damage to the equipment and to surrounding items. However, if it is necessary to operate it inside a building, adequate ventilation must be provided, so that people and animals are not affected. It is imperative that exhaust gases are discharged outside.
7 1.3.6 Filling with fuel The fuel is highly flammable and its vapours are combustible. Smoking, using a naked flame or producing sparks are forbidden while the fuel tank is being filled. Filling should be carried out with the motor turned off. All traces of fuel should be wiped off with a clean cloth. Always place the generating set on a flat, level and horizontal surface to avoid fuel spillage from the tank onto the motor. Storage and handling of petroleum products must be carried out in accordance with the law. Close the fuel tap (if fitted) each time the tank has been filled. Fill the tank using a funnel, taking care not to spill any fuel. Then screw the petrol cap back on to the fuel tank as soon as filling is complete. Never top up fuel when the generating set is in operation or hot Safety guidelines against burns Never touch the motor or the silencer while the generating set is in operation, or when it has just stopped. Warning Hot oil burns, avoid contact with the skin. Check that the system is no longer pressurised before carrying out any procedures. Never start or run the motor when the oil filler cap is off as oil may splash out Safety guidelines for handling batteries Never place the battery close to a flame or fire Use only insulated tools Never use sulphuric acid or acid water to top up the electrolyte level Protecting the environment Never drain or discard used oil onto the ground, but put it into a designated container. As far as possible, try to avoid sound reverberating through walls and buildings, as the noise will be amplified. If the exhaust silencer of your generating set is not fitted with a spark arrester and you need to use it in wooded, bushy or uncultivated areas, be extremely careful and make sure that sparks do not cause a fire (clear vegetation from a fairly large area where you wish to place your generating set) of moving parts Warning Never go near a moving part that is in operation if you have loose clothing or long hair that is not enclosed in a protective hair net. Do not try to stop, slow down or impede a moving part when it is in operation Capacity of the generating set (overload) Never exceed the rated load of the generating set (in Amps and/or Watts) when it is running continuously. Before connecting and operating the generating set, calculate the electrical power required by the electric appliances (in Watts). This electrical power rating is usually found on the manufacturer's plate on bulbs, electrical appliances, motors etc. The sum total of power required by these appliances should not exceed the nominal power rating of the generating set Operating conditions The stated outputs of the generating sets are obtained in example conditions according to ISO : +27 C, 100 m above sea-level, humidity level equal to 60 % or +20 C, 300 m above sea-level, humidity level equal to 60 %. Performance is reduced by approximately 4 % for every additional 10 C and/or approximately 1 % for every additional 100 m in altitude. 2. General description 2.1. Description of the generating set Fuel tank (no. 1, fig. A) Engine (no. 7, fig. A) Starting handle (no. 13, fig. A) Fuel tank plug (no. 2, fig. A) Silencer (no. 8, fig. A) Fuel tap (no. 14, fig. A) Oil filler plugs (no. 3, fig. A) Air filter (no. 9, fig. A) Choke (no. 15, fig. A) Oil drain plugs (no. 4, fig. A) Engine switch (no. 10, fig. A) Circuit breaker (no. 16, fig. A) Earth connection (no. 5, fig. A) Starter recoil reel (no. 11, fig. A) Current transformer switch (no. 17, fig A) Alternator (no. 6, fig. A) Household sockets (no. 12, fig. A)
8 3. Preparation before starting 3.1. Checking the oil level Always check the engine oil level before starting. Checking and topping up should be carried out with the generating set on a horizontal surface. Remove the grey-coloured plug-gauge (no. 1, Fig. B) on the exhaust side by unscrewing it, and wipe the gauge. Insert the gauge into the filler neck (no. 2, Fig. B) without screwing it up. Visually check the level and top up if necessary. Using a funnel, fill the oil sump until it overflows. Screw the cap back up again tightly in the filler tube. Check that there are no leaks. Wipe off excess oil with a clean cloth Checking the fuel level Stop the engine before filling up with fuel and fill up in a well-ventilated area. Do not smoke, or bring naked flames or sparks near to the area where you are filling up with fuel or where the fuel is stored. Only use clean fuel without any water. Do not overfill the tank (there should not be any fuel in the filler neck). When you have filled up, ensure that the tank cap is closed correctly. Take care not to spill any fuel when filling the tank. Before starting up the generating set, and if any fuel has been spilt, make sure that it has dried and that the vapours have cleared away. Check the fuel level and top up if necessary: Unscrew the fuel tank cap (no. 2, fig A). Fill the tank (no. 1, fig A) using a funnel, taking care not to spill petrol. Screw the cap back on to the fuel tank Earthing the generating set To earth the generating set, use a 10 mm2 copper wire attached to the generating set earth connection and to an earthing rod of galvanised steel set in the ground to a depth of 1 metre. This also dissipates the static electricity that builds up in the electrical machines Positioning the generating set for operation Place the generating set on a flat, horizontal surface which is firm enough to prevent the set sinking down (under no circumstances should the set tilt any direction by more than 10 ). Choose a site that is clean, well-ventilated and sheltered from bad weather, and store the additional supplies of oil and fuel within close proximity, although respecting a certain distance for safety. 4. Using the generator set 4.1. Starting procedure Open the petrol tap by turning the control lever (no. 14, fig. A) to the right. Place the knob of the choke (no. 15, fig. A) on closed position as shown on the illustration. Note: Do not use the choke when the engine is warm or when the atmospheric temperature is high. Place the engine switch (no. 10, fig. A) on "ON" or "I". Seize the starting handle (no. 13, fig. A) correctly and pull it slowly until some resistance is felt, then let it return gradually. Take the starting handle again correctly, then pull the cord sharply and rapidly (pull it right out, using both hands if necessary). Allow the handle to return slowly by hand. If the engine has not started, repeat the operation until the engine starts by gradually opening the choke. When the engine has started, gradually open the choke (no. 15, fig. A) Operation When the engine begins to heat up, gradually bring the knob of the choke (no. 15, fig A) to open position. When the running speed of the generating set has stabilised: Check that circuit breaker (no. 16, fig A) is engaged. Connect the plug(s) to the generating set socket(s).
9 4.3. Electric current voltage selection Unplug the connected devices if necessary Put the switch on the desired voltage (no. 17, diag A), then plug back the devices on the sockets 4.4. Switching off Warning When the generating set is turned off, the engine continues to give off heat. Appropriate ventilation should be provided after the generating set is turned off. To stop the generating set urgently, place the engine switch on "OFF" or "О". Take the plugs out of the sockets and allow the engine to run without any charge for 1 to 2 minutes. Place the engine switch (no. 10, fig. A) on "OFF" or "О" and the set will stop. Close the fuel tap (no. 14, fig. A). 5. Safety features (if fitted, see specifications table) 5.1. Oil cut-out This mechanism is designed to prevent any damage to the motor resulting from lack of oil in the motor sump. It automatically cuts out the motor. If the motor stops and will not restart, check the motor oil level before looking for any other cause of the problem Circuit breaker The electrical circuit of the set is protected by several magnetothermal, differential or thermal cut-out switches. Any overload and/or short circuits cause the supply of electrical energy to be cut. 6. Maintenance schedule 6.1. Reminder of use The maintenance interval frequency and the operations to be carried out are outlined in the maintenance programme. However, it should be added that it is the environment in which the generating set is operating which determines this programme. Accordingly, if the set is used in extreme conditions, shorter intervals between maintenance procedures should be adopted. These maintenance schedules apply only to generating sets running on fuel and oil, that conform to the specifications given in this booklet Maintenance table carry out the maintenance procedures at whichever deadline is reached first Each time it is used First month or after the first 20 hours Every 3 months or 50 hours Every 6 months or 100 hours Every 12 months or 300 hours item Engine oil Check the level Change Air filter Check Clean (1) Sediment bowl Clean Spark plug Check / clean Spark arrester Clean Valve clearance Check / adjust (*) Strainer and petrol tank Clean (*) Cleaning the generating set Fuel line Check (replace if necessary) Every 2 years (*) Note: * This procedure should be carried out by one of our registered agents (1) : Perform air filter maintenance more frequently for operation in dusty locations.
10 7. Maintenance procedures 7.1. Cleaning the air filter Never use petrol or solvents with a low flash point for cleaning the air filter element as this could result in a fire or explosion. Remove the wing nut (no. 1, fig. C) attaching the air filter cover (no. 2, fig. C), then remove the latter. Remove the wing nut attaching the filter. Remove the assembly consisting of foam (no. 3, fig. C) and paper (no. 4, fig. C) elements, and separate them. Check carefully that the two elements are not torn or pierced. Replace them if they are damaged. Foam element (no. 3, fig. C): A) Wash the element in a solution of household cleaning product and warm water, then rinse thoroughly, or wash it in nonflammable solvent or solvent with a high flash point. Leave the element to dry fully. B) Soak the element in clean engine oil and remove the excess oil. The engine will smoke when it is started for the first time if too much oil remains in the foam. Paper element (no. 4, fig. C): Tap the element lightly several times on a hard surface to remove excess dirt, or send compressed air through the filter, from the inside outward. Never try to remove dirt using a brush. Replace the element if it is too dirty. Carry out refitting following the reverse procedure to that used for removal Cleaning the sediment bowl Switch off the fuel tap (no. 14, fig. A). Unscrew the plug (no. 1, Fig. D) to drain the fuel. Fit the plug (no.1, Fig. D) back on. Remove the bowl (no. 1, Fig. E) and the seal (no. 2, Fig. E). Wash the bowl (no. 1, Fig. E) with non-flammable solvent or solvent having a high flash point. Leave to dry fully. Refit the seal and the bowl. Open the fuel tap (no.14, Fig. A) and check that there are no leaks Renewing the motor oil Change the oil when the engine is still warm, to ensure that drainage is rapid and complete. Remove the filling plug-gauge (no. 1, fig. B) and the drain plug (no. 3, fig. B) and drain the oil into a suitable container. On completion, screw up again and tighten the drain plug (no. 3, fig. B). Fill the engine oil sump with the recommended oil, then check the level. Put in place and tighten the filling plug-gauge (no. 1, fig. B). Check that there is no oil leak after filling. Wipe off any trace of oil with a clean cloth Cleaning the spark arrester Loosen the three mounting bolts (no. 1, fig. F) and (no. 2, fig. F) from the silencer (no. 3, fig. F), then remove the latter. Loosen the four bolts (no. 4, fig. F) and (no. 5, fig. F) holding the silencer guard (no. 6, fig. F) and then remove silencer guard. Remove the mounting bolt (no. 7, fig. F) from spark arrester (no. 8, fig. F) and place it down. Using a wire brush, remove the carbon deposits from the spark arrester screen. Note: The spark arrester must have no holes or cracks. Replace if necessary. Refit the spark arrester (no. 8, fig. F), the guard (no. 6, fig. F) and the silencer (no. 3, fig. F) in the reverse order to removal Checking the spark plug Remove the spark plug cap and use a spark plug spanner to remove the spark plug. Visually inspect the spark plug and discard it if the electrodes are worn or if the insulation is split or chipped. If it is to be re-used, clean the spark plug with a wire brush. Measure the electrode gap with a feeler gauge. The electrode gap should be from 0.70 to 0.80 mm. Check that the spark plug washer is in good condition and screw the spark plug in by hand, in order to avoid damaging the threads. After fitting the spark plug, tighten it with a spark plug spanner to secure the washer. Note: when fitting a new spark plug, tighten it by 1/2 turn after it is in place, in order to press the washers tightly. For the installation of an old spark plug, tighten it by a 1/8 1/4 turn after it is in place, in order to press the washer tightly.
11 7.6. Checking bolts, nuts and screws Daily, detailed checks of all nuts, bolts and screws are essential in order to prevent any accidents or breakdowns. Inspect the generating set as a whole before and after each use. Tighten any loose nuts or screws. NB: the tightening of cylinder head bolts should be carried out by a specialist. Contact your local agent Cleaning the generating set Remove all dust and debris from around the exhaust and clean the generating set using a cloth and a brush (cleaning with a water jet is not recommended, and cleaning with high-pressure cleaning equipment is forbidden). Carefully clean the motor air inlets and outlets and the alternator. Check the general condition of the generating set and, if necessary, replace any faulty parts. 8. Storing the generating set Generating sets which are to remain unused for a long period of time must undergo certain procedures, in order to keep them in good condition. Check that the storage area is not dusty or humid. Clean the exterior of the generating set and apply rustproofing product. Close the fuel tap (OFF position), remove the sediment bowl and drain it. Open the fuel tap (ON position) and drain the petrol from the tank into a suitable container. Refit the sediment bowl and tighten fully. Drain the carburettor by loosening the drain screw. Collect the petrol in a suitable container. Change the engine oil. Remove the spark plug and pour about 15 ml of oil into the cylinder, then refit the spark plug. Leave the engine to run for a few moments to distribute the oil in the cylinder. Clean the generating set and cover the engine again to protect it from dust. Store the generating set in a clean, dry place. 9. Fault finding Probable causes Remedial action The generating set is being charged during start-up Take it off charge Fuel level too low Fill up with fuel The engine will not The fuel tap is closed Open the fuel tap start Fuel supply blocked or leaking Have the system repaired Blocked air filter Clean the air filter Control on "OFF" or "О" Place the control on "ON" or "I" Defective spark plug Replace the spark plug Probable causes Remedial action The engine cuts out Blocked ventilation inlets Clean the air inlet and outlet guards Probable overcharge Check the charge Probable causes Remedial action Circuit-breaker tripped Reset the circuit breaker Circuit-breaker faulty Have it checked, repaired or replaced No electric current Faulty plug socket Have it checked, repaired or replaced Faulty appliance supply lead Change the lead Faulty alternator Have it checked, repaired or replaced Switched on the wrong position Chande the position Circuit breaker trips Probable causes Remedial action out Faulty equipment or lead Have it checked, repaired or replaced
12 10. Specifications Model HX 3000 TB UK Engine type GX 200 Output (Watts) Direct current X Alternating current 115V/16A 230V/12.2A Socket type 1x10/16A 115V 1x10/16A 230V Circuit breaker Oil guard Battery X Acoustic pressure at 1 m 83 db(a) Weight in kg (without fuel) 41 Dimensions l x w x h in cm 59x46x43 Recommended oil SAE 15W40 Oil sump capacity in L 0.6 Recommended fuel Unleaded petrol Fuel tank capacity in litres 3.6 Spark plug NGK BPR6ES / DENSO : W20 EPR-U : standard : optional X: impossible 11. Cable sizes Rated current Cable lengths (A) 0 50 metres metres metres mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm mm EC Declaration of conformity Name and address of manufacturer SDMO, 12 bis rue de la Villeneuve, CS 92848, BREST CEDEX 2 Description of the equipment Product Generating set Make SDMO Type HX 3000 TB UK Electrical output supplied Rated output: 2240 W G. G. Le Gall, the manufacturer's authorised representative, hereby declares that the product conforms to the following EU Directives: 98/37/EC / Machinery Directive. 73/23/EEC / Low Voltage Directive (modified by Directive 93/68/EEC) 89/336/EEC / Directive on Electromagnetic Compatibility (modified by directives 92/3/EEC and 93/68/EEC) 2000/14/EC / Directive relating to the Noise Emission of Outdoor Equipment For Directive 14 /2000 /EC - Notified Body: CETIM SERVICE DIFFUSION BP 67 F SENLIS - Compliance procedure: Appendix VI - Sound pressure level guaranteed (Lwa) : 96 dba References to harmonized standards used o EN12601/EN1679-1/EN /2006 G. Le Gall
3KVA DUAL VOLTAGE GENERATOR MODEL NO: PG3800DV PART NO: 8857815 OPERATION & MAINTENANCE INSTRUCTIONS LS1016 INTRODUCTION Thank you for purchasing this CLARKE 3KVA Dual Voltage Generator. Before attempting
GENERATOR MODEL NO: FG3000 PART NO: 8857700 OPERATION & MAINTENANCE INSTRUCTIONS LS0609 INTRODUCTION Thank you for purchasing this CLARKE Generator. Before attempting to use this product, please read this
ONTENTS or y handle lug key 800W Generator Original manual Now you have purchased a Workzone product you can rest assured in the knowledge that as well as your 3 year parts and labour guarantee you have
GENERATOR MODEL NO: DG6000DVES PART NO: 8675000 OPERATION & MAINTENANCE INSTRUCTIONS LS1216 INTRODUCTION Thank you for purchasing this CLARKE Generator. Before attempting to use this product, please read
Commercial Series Generator Operator Manual (with Kohler Command series engines) PN: 220880 PREFACE Thank you for purchasing a Wanco Commercial Series portable generator set. This manual contains important
GASOLINE GENERATOR SET USER S MANUAL Foreword Thank you for purchasing our gasoline generator and hope that you will enjoy operating your unit, one of the finest models in the market. This Manual provides
Thank you for purchasing a Honda generator. This manual covers operation and maintenance of the EB3000 and EB4000 generators. All information in this publication is based on the latest product information
Please dispose of packaging for the product in a responsible manner. It is suitable for recycling. Help to protect the environment, take the packaging to the local amenity tip and place into the appropriate
Air Compressor ENGINE DRIVEN Operating & Maintenance Instructions 1110-1 - Read these safety instructions before using the equipment. INTRODUCTION Thank you for purchasing this Clarke portable compressor.
FR GB MANUEL d Utilisation / Instructions for use groupe électrogène / GENERATOR MODÈLES / MODELS CHALLENGER 3000 CHALLENGER 4000 CHALLENGER 5000 CHALLENGER 7000 MU_02GE_CHAL_30_40_50_70_FR_GB Thank you
WARNING Read the instructions before using the machine PETROL DRIVEN POWER WASHER MODEL NO: TIGER1700 PART NO: 7320054 OPERATION & MAINTENANCE INSTRUCTIONS LS0511 2 INTRODUCTION Thank you for purchasing
User manual B950I, B1000i, B2000i, B3000i Always read the user manual thoroughly before using the generator. Never use the generator in a closed room/area. Exhaust may cause suffocation. The exhaust pipe
Part No. 99920-2280-02 FJ180V KAI 4-stroke air-cooled gasoline engine OWNER, S MANUAL SAFETY AWARENESS FOREWORD TABLE OF CONTENTS Whenever you see the symbols shown below, heed their instructions! Always
Owner s Manual GENERATOR EU3000is o2001-2009 Honda Motor Co., Ltd. -All Rights Reserved See page 85 for Initial Use Instructions The engine exhaust from this product contains chemicals known to the State
SAVE THESE INSTRUCTIONS M-150S Series 12-Volt Fuel Pump M-150S-B100-MU Manual Nozzle & M-150S-B100-AU Automatic Nozzle Owner s Manual TABLE OF CONTENTS General Information...2 Safety Instructions...2 Installation...2
GX60 GB Operator s Manual Read the operator s manual carefully and make sure that you understand the contents before using the lawnmower. 967-0 Carton Contents This product may have been purchased with
LAWN MOWER OWNER S MANUAL 1.8kW Petrol Engine 123CC 420mm CUTTING WIDTH MODEL: S421-C SAFETY OPERATION ASSEMBLY MAINTENANCE WARRANTY CAUTION: Read and follow all Safety Rules and Instructions before operating
Battery Backup System STEP-BY-STEP INSTALLATION GUIDE Operating Instructions & Parts Manual ESP25 Please read and save these instructions. Read carefully before attempting to assemble, install, operate
STIGA DINO 45 EURO TORNADO 45 8211-3389-08 SVENSKA S 1. 2. 1 2 3 4 3. 4. FULL ADD ADD FULL 5. 6. STOP G G 7. 8. EURO 2 S SVENSKA 3 2 1 3x 9. 10. 0,76 mm 0,75 mm 11. 12. 40 Nm 13. 3 SVENSKA S 4 GB ENGLISH
PF-4000, PF-4010, PF-4210 MULTI-PURPOSE ENGINE Date 09-26-01 Supplier To The Outdoor Power Equipment Industry ISM, Inc. 1028 4 th Street SW Auburn, WA 98001 Phone: (253) 333-1200 Fax: (253) 333-1212 WWW.TANAKA-USA.COM
Owner s Manual GENERATOR EU2000i o2001-2009 Honda Motor Co., Ltd. -All Rights Reserved See page 82 for Initial Use Instructions The engine exhaust from this product contains chemicals known to the State
HIGH FREQUENCY AUTOMATIC BATTERY CHARGER MODEL NO: HFBC12 PART NO: 6267000 OPERATION & MAINTENANCE INSTRUCTIONS LS0814 INTRODUCTION Thank you for purchasing this CLARKE High Frequency Automatic Battery
FX850V 4 stroke air-cooled V-twin gasoline engine OWNER S MANUAL SAFETY AWARENESS Whenever you see the symbols shown below, heed their instructions! Always follow safe operating and maintenance practices.
User Manual 50620 139CC 4 STROKE PETROL LAWN MOWER www.909.com Read all safety warnings and all instructions thoroughly before operating this product. Contents Pack contents /parts 2 Description of Symbols
GASOLINE POWERED PORTABLE GENERATORS OPERATING AND MAINTENANCE INSTRUCTIONS Generator Models SXA1900HX, SXA2800HX,SXB2800HX SXB4000HX, SXB5500HX(S), SXB7000HX(S) JOHN BROOKS COMPANY LIMITED TORONTO - MONTREAL
Version 3.1 Stand 09.2014 Robert Bosch (Australia) Pty. Ltd. 1555 Centre Road Clayton, Victoria 3168 C3 Operating Instructions For further information please contact Bosch at: Australia 1300 30 70 40 www.boschautoparts.com.au
Owners Manual: - Pumps GENERAL SAFETY RULES 1. The products mentioned in this manual are specially designed for the pre-filtering and re-circulation of water in swimming pools and spas. 2. They are designed
APG3102 TM Owner s Manual 2000 WATT DIGITAL GENERATOR Distributed by: ALL-POWER AMERICA 2005 ALL-POWER AMERICA 16273 E. Gale Ave City Of Industry, California 91745 www.allpoweramerica.com www.allpoweramerica.com
Fuel Filling SAFETY ON THE FORECOURT Petroleum gases are highly inflammable and, in confined spaces, are also extremely explosive. Petroleum gasses are highly flammable, have a low flash point, and are
PETROL ENGINE Model: MLR52 IMPORTANT: Read this manual fully before assembly and use and observe all safety rules and operating instructions Contents Technical Specification 2 Safety 3 Starting 5 Running
DIESEL GENERATOR OPERATIONAL MANUAL ORIGINAL INSTRUCTION ATTENTION 1. Children should be kept at a safe distance from the generator. 2. Don't touch the engine or muffler while generator is in operation.
USE and MAINTENANCE INSTRUCTION MANUAL W-300 W-300 WB LPH-300 GRAVITY SPRAY GUN Series en it fr es pt de se TECHNICAL DATA High T.E.C. series Nozzle_Needle set Combination W-300 WB W-300 W-300-081G 0.8
M. E. Y. EQUIPMENT MOWER MANUAL 200 COLLIER ROAD, BAYSWATER. WESTERN AUSTRALIA 6053 TELEPHONE (08) 9370 1110, FACSIMILE (08) 9370 2566 Web Site: www.mey.com.au Email: firstname.lastname@example.org INTRODUCTION The technical
ELECTRIC CAR POLISHER MODEL NO: CP254 PART NO: 6462108 OPERATION & MAINTENANCE INSTRUCTIONS LS0610 INTRODUCTION Thank you for purchasing this CLARKE electric car polisher. Before attempting to use this
Model VI4300 Digital Inverter Generator User s Manual January 2015 PREFACE Thank you for purchasing a Voltmaster inverter generator. This manual covers the operation and preventive maintenance of the VI4300
- 1 - Contents 1. Safety Point for Attention...1 2. Parts & Subassemblies...2 3. Check-ups before Operation...3 4. Starting of generator...6 5. Usage of Generator...9 6. Stopping of generator...12 7. Maintenance...13
OWNERS MANUAL Models: SP3, SPSS3 Automatic Battery Charger PLEASE SAVE THIS OWNERS MANUAL AND READ BEFORE EACH USE. This manual will explain how to use the charger safely and effectively. Please read and
Owner s Manual PUMP WB20XT/WB30XT 201 Honda Motor Co., Ltd. All Rights Reserved The engine exhaust from this product contains chemicals known to the State of California to cause cancer, birth defects or
Electric Trolling Motor L Series User s Manual Please read and retain this manual before using product REACH RoHS TABLE OF CONTENTS Contents GENERAL INFORMATION 4 SPECIFICATIONS 4 WIRING AND BATTERY RECOMMENDATIONS
FOR SAFE OPERATION WARNING: * To prevent fire hazards and to provide adequate ventilation, keep the engine at least 3 ft away from buildings and other equipment, during operation. * Do not place flammable
muck-truck It doesn t cost the earth to move it! PEDESTRIAN DUMPER MKIII OWNERS & OPERATIONS INSTRUCTION MANUAL CONGRATULATIONS! And thank you for purchasing a new muck-truck. We have done our utmost to
OWNER S MANUAL BATTERY BACKUP SUMP Installation Operation Parts For further operating, installation or maintenance assistance, Call 98-8-05 PRINTED IN U.S.A. M-8 (/9) RULES FOR SAFE INSTALLATION AND OPERATION
KIPOR POWER CO., LTD. SINEMASTER DIGITAL GENERATOR KGE3000Ti PREFACE Thank you for purchasing a kipor generator. This manual covers operation and maintenance of the KGE3000Ti Inverter generator. All information
WHAT S IN THE BOX HIGH PRESSURE PETROL WATER PUMP 196CC 4 STROKE INSTRUCTION MANUAL SPECIFICATIONS Motor: 4.85kW (6.5HP) Engine: 4 Stroke, air cooled Fuel Type: Unleaded Fuel Tank Capacity: 3.6L Engine
Air Compressor PP10ND PPH10ND PP15ND PPH15ND Operating & Maintenance Instructions 1002 SPECIFICATIONS PP10ND PPH10ND PP15ND PPH15ND Part Number 2090940 2090960 209080 2090100 WARNING! DO NOT ATTEMPT TO
Instruction Manual CORDLESS DRILL 18V Li-ion WITH IMPACT FUNCTION Model SROM 1172 Our tool range has you covered for DIY. Whatever the job, make light work of it with MAKO tools. Product Features: 1. Keyless
Thank you for purchasing a Sealey product. Manufactured to a high standard this product will, if used according to these instructions and properly maintained, give you years of trouble free performance.
PETROL POST INCLUDES 150MM AUGER BIT HIGH TORQUE POWER HEAD HOLE DIGGER ONE PERSON OPERATION ALL STEEL REDUCTION DRIVE GEARBOX K16031 ED2 Sept 15 Table of Contents PETROL POST HOLE DIGGER Know Your Product...1
User Manual 140CC 4 STROKE PETROL LAWN MOWER www.909.com Read all safety warnings and all instructions thoroughly before operating this product. Contents Pack contents /parts 2 Intended use of the 140cc
symbols and decals Xxxx xxx xxxx xx xxxx x xxxx. Used in this publication to notify the reader of a risk of personal injury, particularly if the reader DOES NOT follow the instructions given in the manual.
52731 18 AMP-HOUR 12 VOLT OVERHEAT PROTECTION JUMP START OWNER S MANUAL PORTABLE POWER COMPACT & ROBUST 18 Amp-Hour, 12 Volt Wall charger 6-gauge booster cable Built in ultra-bright LED work light Safety
GEN 5.0 Generator Service Manual IMPORTANT: Read all safety precautions and instructions carefully before operating equipment. Refer to operating instruction of equipment that this engine powers. Ensure
R R WUXI KIPOR POWER CO., LTD. DIESEL GENERATING SET Single-phase: KDE16EA K DE16STA KDE19EA K DE19STA Three-phase: KDE16EA3 K DE16STA3 KDE19EA3 K DE19STA3 PREFACE Thank you for purchasing a our generating
Single Speed Diesel Power Unit Model HPD11 Maximum Operating Pressure 510 bar ABSOLUTE EQUIPMENT PTY LTD 2/186 Granite Street, GEEBUNG QLD 4034 Australia email@example.com Phone: +61 7 3865
Page 1 of 8 Marks & Meanings DANGER: Keep the pump equipment out of the reach of children! Warns that the failure to follow the directions given could cause serious risk to individuals or objects. WARNING:
GEN3500 i 3,000 MAX WATTS INVERTER GENERATOR INSTRUCTION MANUAL READ ALL INSTRUCTIONS AND WARNINGS BEFORE USING THIS PRODUCT. This manual provides important information on proper operation & maintenance.
RECHARGEABLE SPOTLIGHT MODEL: RWL10 Part No: 4002822 INSTRUCTION MANUAL LS0609 INTRODUCTION Thank you for purchasing this CLARKE product Before attempting to use the product, it is essential that you read
EN Installation manual portable distributors EN 60003206 Issue 11.2016 15/11/2016 Table of contents 1 About this manual 3 1.1 Structure of the warnings 3 1.2 Symbols used 4 1.3 Signal words used 4 2 Intended
INSTANT JUMPSTARTING POWER USER MANUAL Copyright PowerStation, LLC All rights reserved MODEL: PS1100 CONTENTS Warning Info 1 2 Introduction 3 Features 3 Getting to know your PS1100 4 5 Operation 6 Charging
LV48EA/LV48XA LV56EA/LV56XA LV95EA/LV95XA (LEV90-0) Four-Cycle Engine Vertical Crankshaft Air-Cooled Table of Contents IMPORTANT NOTICE! Safety Definitions...ii I. General Safety Precautions... II. How
EN ESS FRC KT610-KT620, KT715-KT745 Owner's Manual IMPORTANT: Read all safety precautions and instructions carefully before operating equipment. Refer to operating instruction of equipment that this engine
MOTORINI GP 50 User s Manual www.motorini.co.uk Dear user: Thank you for choosing to buy a Motorini GP 50 This manual provides the correct operation and maintenance methods for safe riding and maintaining
MODEL 600A 6 VOLT BATTERY CHARGER ASSOCIATE IMPORTANT SAFETY INSTRUCTIONS. SAVE THESE INSTRUCTIONS. This manual contains important safety and operating instructions for the battery charger you have purchased.
Generator OWNER S MANUAL Read this manual carefully before operating this machine. PRO.8 i 7VU-899-L - Read this manual carefully before operating this machine. This manual should stay with this machine
Thank you for purchasing a Honda engine. This manual covers the operation and maintenance of GX 110 and GX 140 engines. All information in this publication is based on the latest product information available
R WUXI KIPOR POWER CO., LTD. GASOLINE GENERATOR Single-phase: KGE1E KGE1EA KGE13EA Three-phase: KGE1E3 KGE1EA3 KGE13EA3 PREFACE Thank you for your purchase of our unit, our aim is to provide a high-quality
EN Installation manual wall-mounted distributor EN 60003233 Issue 11.2016 2016-14-11 Table of contents 1 About this manual 3 1.1 Structure of the warnings 3 1.2 Symbols used 4 1.3 Signal words used 4 2
TRE 070 TRE 0702 TRE 080 FR EN DE IT NL ES PT EL TR MK NO SV DA FI CS PL HU RU HR SL MANUEL D UTILISATION OPERATOR S MANUAL GEBRAUCHSANWEISUNG MANUALE DI ISTRUZIONI GEBRUIKERSHANDLEIDING MANUAL DE INSTRUCCIONES
Powerland Tri Fuel Generator Owner s Manual Full Power Output Panel SERIES GASOLINE, LPG, NG POWER This manual provides information regarding the operation and maintenance of these products. We have made
Operating Instructions SHORTENING FILTER INSPECT CARTON MODEL NO'S 102 & 107 CE Series Remove product from carton... If damaged : Notify carrier Save carton and packing material Contact your Dealer, Distributor
CORROSION PREVENTION AND APPEARANCE CARE SECTION 6 Corrosion prevention and appearance care Protecting your Toyota from corrosion......................... 382 Washing and waxing your Toyota.............................