2 Construction of synchronous machines In a synchronous generator, a DC current is applied to the rotor winding producing a rotor magnetic field. The rotor is then turned by external means producing a rotating magnetic field, which induces a 3-phase voltage within the stator winding. Field windings are the windings producing the main magnetic field (rotor windings armature windings are the windings where the main voltage is induced (stator windings)
3 Construction of synchronous machines The rotor of a synchronous machine is a large electromagnet. The magnetic poles can be either salient (sticking out of rotor surface) or nonsalient construction. Non-salient-pole rotor: usually two- and four-pole rotors. Salient-pole rotor: four and more poles. Rotors are made laminated to reduce eddy current losses.
4 Construction of synchronous machines Two common approaches are used to supply a DC current to the field circuits on the rotating rotor: 1. Supply the DC power from an external DC source to the rotor by means of slip rings and brushes; 2. Supply the DC power from a special DC power source mounted directly on the shaft of the machine. Slip rings are metal rings completely encircling the shaft of a machine but insulated from it. Graphite-like carbon brushes connected to DC terminals ride on each slip ring supplying DC voltage to field windings.
5 Construction of synchronous machines On large generators and motors, brushless exciters are used. A brushless exciter is a small AC generator whose field circuits are mounted on the stator and armature circuits are mounted on the rotor shaft. The exciter generator s 3-phase output is rectified to DC by a 3-phase rectifier (mounted on the shaft) and fed into the main DC field circuit. It is possible to adjust the field current on the main machine by controlling the small DC field current of the exciter generator (located on the stator).
6 Construction of synchronous machines A brushless exciter: a low 3-phase current is rectified and used to supply the field circuit of the exciter (located on the stator). The output of the exciter s armature circuit (on the rotor) is rectified and used as the field current of the main machine.
7 Construction of synchronous machines To make the excitation of a generator completely independent of any external power source, a small pilot exciter is often added to the circuit. The pilot exciter is an AC generator with a permanent magnet mounted on the rotor shaft and a 3-phase winding on the stator producing the power for the field circuit of the exciter.
8 Construction of synchronous machines A rotor of large synchronous machine with a brushless exciter mounted on the same shaft.
9 Construction of synchronous machines Exciter Salient poles.
10 Rotation speed of synchronous generator By the definition, synchronous generators produce electricity whose frequency is synchronized with the mechanical rotational speed. f p 120 e n m Where f e is the electrical frequency, Hz; n m is the rotor speed of the machine, rpm; p is the number of poles. Steam turbines are most efficient when rotating at high speed; therefore, to generate 60 Hz, they are usually rotating at 3600 rpm (2-pole). Water turbines are most efficient when rotating at low speeds ( rpm); therefore, they usually turn generators with many poles.
11 The induced voltage in a 3-phase set of coils In three coils, each of N C turns, placed around the rotor magnetic field, the induced in each coil will have the same magnitude and phases differing by : e ( t) N cos t aa' C m m e ( t) N cos t 120 bb' C m m e ( t) N cos t 240 cc' C m m Peak voltage: E N Emax 2N Cf max C m RMS voltage: E A 2 N 2 C f 2N f C
12 Internal generated voltage of a synchronous generator The magnitude of internal generated voltage induced in a given stator is E 2N f K A where K is a constant representing the construction of the machine, is flux in it and is its rotation speed. C Since flux in the machine depends on the field current through it, the internal generated voltage is a function of the rotor field current. Magnetization curve (open-circuit characteristic) of a synchronous machine
13 Equivalent circuit of a synchronous generator The internally generated voltage in a single phase of a synchronous machine E A is not usually the voltage appearing at its terminals. It equals to the output voltage V only when there is no armature current in the machine. The reasons that the armature voltage E A is not equal to the output voltage V are: 1. Distortion of the air-gap magnetic field caused by the current flowing in the stator (armature reaction); 2. Self-inductance of the armature coils; 3. Resistance of the armature coils;
14 Equivalent circuit of a synchronous generator Armature reaction: When the rotor of a synchronous generator is spinning, a voltage E A is induced in its stator. When a load is connected, a current starts flowing creating a magnetic field in machine s stator. This stator magnetic field B S adds to the rotor (main) magnetic field B R affecting the total magnetic field and, therefore, the phase voltage. Lagging load
15 Equivalent circuit of a synchronous generator The load current I A will create a stator magnetic field B S, which will produce the armature reaction voltage E stat. Therefore, the phase voltage will be The net magnetic flux will be V E E A stat B B B net R S Rotor field Stator field
16 Equivalent circuit of a synchronous generator Since the armature reaction voltage lags the current by 90 degrees, it can be modeled by E stat jxi A The phase voltage is then V E jxi A A However, in addition to armature reactance effect, the stator coil has a self-inductance L A (X A is the corresponding reactance) and the stator has resistance R A. The phase voltage is thus V E A jxi A jx AI A RI A
17 Equivalent circuit of a synchronous generator Often, armature reactance and selfinductance are combined into the synchronous reactance of the machine: X X X S Therefore, the phase voltage is V E A jx SI A RI A A The equivalent circuit of a 3-phase synchronous generator is shown. The adjustable resistor R adj controls the field current and, therefore, the rotor magnetic field.
18 Equivalent circuit of a synchronous generator A synchronous generator can be Y- or -connected: The terminal voltage will be V 3V fory V V for T T
19 Equivalent circuit of a synchronous generator Since for balanced loads the three phases of a synchronous generator are identical except for phase angles, per-phase equivalent circuits are often used.
20 Phasor diagram of a synchronous generator (similar to that of a transformer) Since the voltages in a synchronous generator are AC voltages, they are usually expressed as phasors. A vector plot of voltages and currents within one phase is called a phasor diagram. A phasor diagram of a synchronous generator with a unity power factor (resistive load) Lagging power factor (inductive load): a larger than for leading PF internal generated voltage E A is needed to form the same phase voltage. Leading power factor (capacitive load).
21 Measuring parameters of synchronous generator model The three quantities must be determined in order to describe the generator model: 1. The relationship between field current and flux (and therefore between the field current I F and the internal generated voltage E A ); 2. The synchronous reactance; 3. The armature resistance.
22 Open circuit Test The generator is rotated at the rated speed, all the terminals are disconnected from loads, the field current is set to zero first. Next, the field current is increased in steps and the phase voltage (whish is equal to the internal generated voltage E A since the armature current is zero) is measured. Since the unsaturated core of the machine has a reluctance thousands times lower than the reluctance of the air-gap, the resulting flux increases linearly first. When the saturation is reached, the core reluctance greatly increases causing the flux to increase much slower with the increase of the mmf.
23 Short Circuit Test In here, the generator is rotated at the rated speed, with the field current is set to zero first, and all the terminals are shortcircuited through ammeters. Next, the field current is increased in steps and the armature current I A is measured as the field current is increased. The plot of armature current (or line current) vs. the field current is the short-circuit characteristic (SCC) of the generator.
24 Short Circuit Test The SCC is a straight line since, for the short-circuited terminals, the magnitude of the armature current is I A R E A X 2 2 A S The equivalent generator s circuit during SC The resulting phasor diagram
25 Short circuit test An approximate method to determine the synchronous reactance X S at a given field current: 1. Get the internal generated voltage E A from the OCC at that field current. 2. Get the short-circuit current I A,SC at that field current from the SCC. 3. Find X S from X S E I A A, SC Since the internal machine impedance is E Z R X X since X R 2 2 A S A S S S A I A, SC
26 OCC and SCC A drawback of this method is that the internal generated voltage E A is measured during the OCC, where the machine can be saturated for large field currents, while the armature current is measured in SCC, where the core is unsaturated. Therefore, this approach is accurate for unsaturated cores only. The approximate value of synchronous reactance varies with the degree of saturation of the OCC. Therefore, the value of the synchronous reactance for a given problem should be estimated at the approximate load of the machine. The winding s resistance can be approximated by applying a DC voltage to a stationary machine s winding and measuring the current. However, AC resistance is slightly larger than DC resistance (skin effect).
27 Example Example 7.1: A 200 kva, 480 V, 50 Hz, Y-connected synchronous generator with a rated field current of 5 A was tested and the following data were obtained: 1. V T,OC = 540 V at the rated I F. 2. I L,SC = 300 A at the rated I F. 3. When a DC voltage of 10 V was applied to two of the terminals, a current of 25 A was measured. Find the generator s model at the rated conditions (i.e., the armature resistance and the approximate synchronous reactance). Since the generator is Y-connected, a DC voltage was applied between its two phases. Therefore: 2R R A A V I DC DC VDC I 225 DC
28 Example (cont.) The internal generated voltage at the rated field current is VT 540 EA V, OC 311.8V 3 3 The synchronous reactance at the rated field current is precisely E X Z R R A 2 2 S S A 2 A 2 I A, SC 300 We observe that if X S was estimated via the approximate formula, the result would be: X S EA I 300 A, SC Which is close to the previous result. The error ignoring R A is much smaller than the error due to core saturation.
29 The Synchronous generator operating alone The behavior of a synchronous generator varies greatly under load depending on the power factor of the load and on whether the generator is working alone or in parallel with other synchronous generators. Although most of the synchronous generators in the world operate as parts of large power systems, we start our discussion assuming that the synchronous generator works alone. Unless otherwise stated, the speed of the generator is assumed constant.
30 The Synchronous generator operating alone Effects of load changes A increase in the load is an increase in the real and/or reactive power drawn from the generator. Since the field resistor is unaffected, the field current is constant and, therefore, the flux is constant too. Since the speed is assumed as constant, the magnitude of the internal generated voltage is constant also. Assuming the same power factor of the load, change in load will change the magnitude of the armature current I A. However, the angle will be the same (for a constant PF). Thus, the armature reaction voltage jx S I A will be larger for the increased load. Since the magnitude of the internal generated voltage is constant E V jx I A S A Armature reaction voltage vector will move parallel to its initial position.
31 The Synchronous generator operating alone Increase load effect on generators with Lagging PF Leading PF Unity PF
32 The Synchronous generator operating alone Generally, when a load on a synchronous generator is added, the following changes can be observed: 1. For lagging (inductive) loads, the phase (and terminal) voltage decreases significantly. 2. For unity power factor (purely resistive) loads, the phase (and terminal) voltage decreases slightly. 3. For leading (capacitive) loads, the phase (and terminal) voltage rises. Effects of adding loads can be described by the voltage regulation: VR V nl V V fl fl 100% Where V nl is the no-load voltage of the generator and V fl is its full-load voltage.
33 The Synchronous generator operating alone A synchronous generator operating at a lagging power factor has a fairly large positive voltage regulation. A synchronous generator operating at a unity power factor has a small positive voltage regulation. A synchronous generator operating at a leading power factor often has a negative voltage regulation. Normally, a constant terminal voltage supplied by a generator is desired. Since the armature reactance cannot be controlled, an obvious approach to adjust the terminal voltage is by controlling the internal generated voltage E A = K. This may be done by changing flux in the machine while varying the value of the field resistance R F, which is summarized: 1. Decreasing the field resistance increases the field current in the generator. 2. An increase in the field current increases the flux in the machine. 3. An increased flux leads to the increase in the internal generated voltage. 4. An increase in the internal generated voltage increases the terminal voltage of the generator.
34 Power and torque in synchronous generators A synchronous generator needs to be connected to a prime mover whose speed is reasonably constant (to ensure constant frequency of the generated voltage) for various loads. The applied mechanical power is partially converted to electricity P Where is the angle between E A and I A. Pin appm 3E I cos conv ind m A A The power-flow diagram of a synchronous generator.
35 Power and torque in synchronous generators The real output power of the synchronous generator is P 3V I cos 3V I cos out T L A The reactive output power of the synchronous generator is Q 3V I sin 3V I sin out T L A Recall that the power factor angle is the angle between V and I A and not the angle between V T and I L. In real synchronous machines of any size, the armature resistance R A << X S and, therefore, the armature resistance can be ignored. Thus, a simplified phasor diagram indicates that I A E cos A sin X S
36 Power and torque in synchronous generators Then the real output power of the synchronous generator can be approximated as P out 3VE sin We observe that electrical losses are assumed to be zero since the resistance is neglected. Therefore: P conv Here is the torque angle of the machine the angle between V and E A. The maximum power can be supplied by the generator when = 90 0 : A X S P out P max 3VE A X S
37 Power and torque in synchronous generators The maximum power specified is called the static stability limit of the generator. Normally, real generators do not approach this limit: full-load torque angles are usually between 15 0 and The induced torque is kb B kb B kb B ind R S R net R net sin Notice that the torque angle is also the angle between the rotor magnetic field B R and the net magnetic field B net. Alternatively, the induced torque is ind 3VE sin m A X S
Synchronous Generators I Spring 2013 Construction of synchronous machines In a synchronous generator, a DC current is applied to the rotor winding producing a rotor magnetic field. The rotor is then turned
Source: POWER GENERATION HANDBOOK CHAPTER 31 SYNCHRONOUS GENERATORS Synchronous generators or alternators are synchronous machines that convert mechanical energy to alternating current (AC) electric energy.
Unit 32 Three-Phase Alternators Objectives: Discuss the operation of a three-phase alternator. Explain the effect of rotation speed on frequency. Explain the effect of field excitation on output voltage.
Induction Motors Revised October 6, 008 EEL 311 ( 008, H. Zmuda) 6. Induction Motors 1 Induction Motors: We just learned how damper or amortisseur windings on a synchronous motor could develop a starting
694 Electric Machines 9.1 A 4-pole wound-rotor induction motor is used as a frequency changer. The stator is connected to a 50 Hz, 3-phase supply. The load is connected to the rotor slip rings. What are
Chapter 2 PRINCIPLES OF AFPM MACHINES In this chapter the basic principles of the AFPM machine are explained in details. Considerable attention is given to the magnetic circuits, windings, torque production,
Experiment 1 The Wound-Rotor Induction Motor Part I OBJECTIVE To examine the construction of the three-phase wound-rotor induction motor. To understand exciting current, synchronous speed and slip in a
10. Starting Method for Induction Motors A 3-phase induction motor is theoretically self starting. The stator of an induction motor consists of 3-phase windings, which when connected to a 3-phase supply
ELECTRICAL MACHINES-II LABORATORY MANUAL T. ANIL KUMAR Associate Professor Department of Electrical and Electrical Engineering N. SINDHU Assistant Professor Department of Electrical and Electrical Engineering
VIII. Three-phase Induction Machines (Asynchronous Machines) Induction Machines 1 Introduction Three-phase induction motors are the most common and frequently encountered machines in industry simple design,
Fachpraktikum Elektrische Maschinen Theory of Induction Machines Prepared by Arda Tüysüz January 2013 Fundamentals Induction machines (also known as asynchronous machines) are by far the most common type
PRACTICAL WORK BOOK For Academic Session 2013 Electrical Machines-I (EE-241) For S.E (EE) Name: Roll Number: Class: Batch: Department : Semester/Term: NED University of Engineer ing & Technology Electrical
Lesson 16: Asynchronous s/induction s ET 332b Ac Motors, s and Power Systems et332bind.ppt 1 Learning Objectives After this presentation you will be able to: Explain how an induction generator erates List
Induction type Energy meter Construction The four main parts of an energy meter are: Driving system Moving system Braking system and Registering system The construction is as shown below: Fig. Construction
SRI VIDYA COLLEGE OF ENGINEERING & TECHNOLOGY QUESTION BANK UNIT III EC6352-ELECTRICAL ENGINEERING AND INSTRUMENTATION UNIT III PART A INDUCTION MOTORS 1. What are the 2 types of 3phase induction motor?
DC Generators INTRODUCTION A generator is a machine that converts mechanical energy into electrical energy by using the principle of magnetic induction. Principle Whenever a conductor is moved within a
ARCHIVES OF ELECTRICAL ENGINEERING VOL. 66(1), pp. 199-206 (2017) DOI 10.1515/aee-2017-0015 Asynchronous slip-ring motor synchronized with permanent magnets TADEUSZ GLINKA, JAKUB BERNATT Institute of Electrical
Exercise 3-1 Armature Reaction and Saturation Effect EXERCISE OBJECTIVE When you have completed this exercise, you will be able to demonstrate some of the effects of armature reaction and saturation in
Just what is an alternator? An alternator is the device used to produce the electricity the car needs to run and to keep the battery charged. The battery is the heart of your electrical system. But you
Moog Components Group manufactures a comprehensive line of brush-type and brushless motors, as well as brushless controllers. The purpose of this document is to provide a guide for the selection and application
Inverter control of low speed Linear Induction Motors Stephen Colyer, Jeff Proverbs, Alan Foster Force Engineering Ltd, Old Station Close, Shepshed, UK Tel: +44(0)1509 506 025 Fax: +44(0)1509 505 433 e-mail:
Part I: Objective type questions and answers Chapter 3.2: Electric Motors 1. The synchronous speed of a motor with 6 poles and operating at 50 Hz frequency is. a) 1500 b) 1000 c) 3000 d) 750 2. The efficiency
EXPERIMENT Induction motor with Matlab Three-Phase Induction Motors 208V LL OBJECTIVE This experiment demonstrates the performance of squirrel-cage induction motors and the method for deriving electrical
EE 742 Chap. 7: Wind Power Generation Y. Baghzouz Fall 2011 Overview Environmental pressures have led many countries to set ambitious goals of renewable energy generation. Wind energy is the dominant renewable
Jacek F. Gieras Rong-Jie Wang Maarten J. Kamper Axial Flux Permanent Magnet Brushless Machines Second Edition Springer Contents 1 Introduction 1 1.1 Scope 1 1.2 Features 1 1.3 Development of AFPM Machines
ECEg439:-Electrical Machine II 2.2 Main Structural Elements of DC Machine Construction of DC Machines A DC machine consists of two main parts 1. Stationary Part (Stator):-It is designed mainly for producing
Exercise 2 Permanent Magnet DC Motor Operating as a Generator EXERCIE OBJECTIVE When you have completed this exercise, you will be familiar with the construction of permanent magnet dc motors as well as
Lecture 20: Stator Control - Stator Voltage and Frequency Control Speed Control from Stator Side 1. V / f control or frequency control - Whenever three phase supply is given to three phase induction motor
Unit-I MEASURING INSTRUMENTS 1.1 Definition of instruments: An instrument is a device in which we can determine the magnitude or value of the quantity to be measured. The measuring quantity can be voltage,
Measurement and Analysis of the Operation of a Single-Phase Induction Motor In class I have shown you the carcass of a four-pole, single phase, ¼ HP motor in varying stages of disassembly. In this lab,
EXPERIMENT 12 Direction of Rotation of Three-Phase Motor PURPOSE: To discover the factors affecting the direction of rotation and speed of three-phase motors. BRIEFING: The stators of three-phase motors
HCI 34E/44E - Technical Data Sheet SPECIFICATIONS & OPTIONS STANDARDS Newage Stamford industrial generators meet the requirements of BS EN 60034 and the relevant section of other international standards
BRUSHLESS EXCITERS FOR TURBINE GENERATORS Economical, Manpower Saving Exciters Based on State-of-the-Art Technology. Mitsubishi Electrical manufactures brushless exciters for all types of turbine generator,
HCI 34F/44F - Technical Data Sheet HCI34F/44F SPECIFICATIONS & OPTIONS STANDARDS Newage Stamford industrial generators meet the requirements of BS EN 60034 and the relevant section of other international
Unit III A.C. Machines - Principle of operation of 3-phase Induction Motor Torque, slips characteristics- Speed control methods Single-phase Induction motor starting methods Principle of operation of Alternators.
Types of Electric Motors Electric Motors DC Motors AC Motors Other Motors Shunt motor Separately Excited motor Induction motor Stepper motor Brushless DC motor Series Motor Permanent Magnet DC (PMDC) Synchronous
UCI224F - Technical Data Sheet UCI224F SPECIFICATIONS & OPTIONS STANDARDS Newage Stamford industrial generators meet the requirements of BS EN 60034 and the relevant section of other international standards
Introduction to Pekik Argo Dahono Electrical Energy Conversion Research Laboratory Institute of Technology Bandung Why Electric Drives Electric drives are available in any power. They cover a wide range
Motor Basics AGSM 325 Motors vs Engines Motors convert electrical energy to mechanical energy. Engines convert chemical energy to mechanical energy. 1 Motors Advantages Low Initial Cost - $/Hp Simple &
Meiden 4-Pole Synchronous Generators Our high-quality, high-efficiency, and compact generators respond to multiplex needs of our customers. Since Meidensha was founded in 1897, our generators have always
DESIGN AND ANALYSIS OF NEW CLASS BRUSHLESS D.C MOTOR (FSM) Tefera Kitaba 1, Dr.A.Kavitha 2, DEEE, Anna University CEG Campus Chennai, India. firstname.lastname@example.org, Department of Electrical and Electronics
CHAPTER 17 SINGLE-PHASE MOTORS INTRODUCTION Single-phase AC motors are the most common motors built. Every home, workshop, and vessel has them. Since there is such a wide variety of these motors, it is
Letra de código Código de rotor bloqueado Rotor bloqueado, Letra de código kva / hp kva / hp A 0.00 3.15 L 9.00 10.00 B 3.15 3.55 M 10.00 11.00 C 3.55 4.00 N 11.00 12.50 D 4.00 4.50 P 12.50 14.00 E 4.50
UCI274D - Winding 311 Technical Data Sheet UCI274D SPECIFICATIONS & OPTIONS STANDARDS WINDINGS & ELECTRICAL PERFORMANCE Stamford industrial generators meet the requirements of BS EN 60034 and the relevant
P734H - Technical Data Sheet Standards STAMFORD industrial alternators meet the requirements of the relevant parts of the BS EN 60034 and the relevant section of other international standards such as BS5000,
Photographs of large cities, such as Seattle, Washington, are visible reminders of how much people rely on electrical energy. Generating Electric Current How is voltage induced in a conductor? According
Chapter 22: Electric motors and electromagnetic induction The motor effect movement from electricity When a current is passed through a wire placed in a magnetic field a force is produced which acts on
Twenty Ways to Optimize Energy Efficiency in the Use of Induction Motors Course No: M06-021 Credit: 6 PDH A. Bhatia Continuing Education and Development, Inc. 9 Greyridge Farm Court Stony Point, NY 10980
Renewable Energy Permanent Magnet DC Motor Courseware Sample 86357-F0 A RENEWABLE ENERGY PERMANENT MAGNET DC MOTOR Courseware Sample by the staff of Lab-Volt Ltd. Copyright 2011 Lab-Volt Ltd. All rights
Induction Motor Control A much misunderstood yet vitally important facet of electrical engineering. The Induction Motor A very major consumer of electrical energy in industry today. The major source of
88 CHAPTER 5 ROTOR RESISTANCE CONTROL OF WIND TURBINE GENERATORS 5.1 INTRODUCTION The advances in power electronics technology have enabled the use of variable speed induction generators for wind energy
Commission 400Hz Power Supply Jonathan Yazenga Zyambo A dissertation submitted to the, University of Cape Town, in fulfilment of the requirements for the degree of Bachelor of Science in Mechatronics Engineering.
LVI634E - Technical Data Sheet LVI634E SPECIFICATIONS & OPTIONS STANDARDS Newage Stamford industrial generators meet the requirements of BS EN 60034 and the relevant section of other international standards
ASSISTANT EXECUTIVE ENGINEER (ELEC.) QUESTIONS & ANSWERS 1. A ceiling fan uses A) split-phase motor B) capacitor start and capacitor run motor C) capacitor start motor D) universal motor 2. High frequency
Small step, big impact: Energy efficiency and dynamic performance The innovative synchronous-reluctance drive system with SIMOTICS motors and SINAMICS converters A new dimension of efficiency siemens.com/reluctance-drive-system
Part-I: Objective type Questions and Answers Chapter 3.1: Electrical System 1. The heat input required for generating one kilo watt-hour of electrical output is called as. a) Efficiency b) Heat Rate c)
UCM274H - Technical Data Sheet UCM274H SPECIFICATIONS & OPTIONS STANDARDS Marine generators may be certified to Lloyds, DnV, Bureau Veritas, ABS, Germanischer-Lloyd or RINA. Other standards and certifications
(approx. 1.5 h) (11/9/15) Introduction In 1819, during a lecture demonstration, the Danish scientist Hans Christian Oersted noticed that the needle of a compass was deflected when placed near a current-carrying
41-100K 2.0 CONSTRUCTION AND OPERATION The type CO relays consist of an overcurrent unit (CO), either an Indicating Switch (ICS) or an ac Auxiliary Switch (ACS) and an Indicating Instantaneous Trip unit
1. A ceiling fan uses A) split-phase motor B) capacitor start and capacitor run motor C) capacitor start motor D) universal motor 2. High frequency transformers sometimes make use of ferrite cores because
SERVICE SHOP NOTES LIMA MAC SELF VOLTAGE REGULATED GENERATORS Troubleshooting Tips Symptom: Engine bogs down or stalls even at no load. Problem: Main stator has one or more taps wound or connected incorrectly.
UMP - MONITORING UNBALANCED MAGNETIC PULL AND AIR-GAP MONITORING FOR LARGE HYDROGENERATORS AN INNOVATIVE MEASUREMENT DEVICE FOR THE MONITORING OF STATOR AND ROTOR MAGNETIC CIRCUITS Dr. Mai Tuxuan, Prof.
Fachpraktikum Elektrische Maschinen Experiments with a 400/ 690 V Squirrel Cage Induction Machine Prepared by Arda Tüysüz January 2013 1. Questions to answer before the experiment - Describe the operation
INDEX NO. : M-145 TECHNICAL MANUAL FOR EFFECT OF CAPACITOR ON STARTING & RUNNING OF SINGLE PHASE INDUCTION MOTOR Manufactured by : PREMIER TRADING CORPORATION 212/1, Mansarover Civil Lines, MEERUT. Phone
This article was downloaded by: [22.214.171.124] On: 21 March 2014, At: 17:37 Publisher: Taylor & Francis Informa Ltd Registered in England and Wales Registered Number: 1072954 Registered office: Mortimer
HCI634H - Technical Data Sheet HCI634H SPECIFICATIONS & OPTIONS STANDARDS Newage Stamford industrial generators meet the requirements of BS EN 60034 and the relevant section of other international standards
How to: Test & Evaluate Motors in Your Application Table of Contents 1 INTRODUCTION... 1 2 UNDERSTANDING THE APPLICATION INPUT... 1 2.1 Input Power... 2 2.2 Load & Speed... 3 2.2.1 Starting Torque... 3
Synchronous motor with fluid coupling drive arrangement for a preheater ID Fan presenter Nathan Schachter SLC PLC Lubrication units Cooling Water DCS SUB BD Breaker SR469 GE STAT-XTOR PLC Field Application
Chapter 21 Electromagnetic Induction and Faraday s Law Chapter 21 Induced EMF Faraday s Law of Induction; Lenz s Law EMF Induced in a Moving Conductor Changing Magnetic Flux Produces an E Field Inductance
LSA 44.3 70 to 150 kva - 50 Hz / 88 to 188 kva - 60 Hz Electrical and mechanical data Specially adapted to applications The LSA 44.3 alternator is designed to be suitable for typical generator applications,
This webinar brought to you by the Relion product family Advanced protection and control IEDs from ABB Relion. Thinking beyond the box. Designed to seamlessly consolidate functions, Relion relays are smarter,
Experiment o. 1 AME OF THE EXPERIMET To study the constructional features of ammeter, voltmeter, wattmeter and energymeter. OBJECTIVE 1. To be conversant with the constructional detail and working of common
University f Jordan School of Engineering Department of Mechatronics Engineering Electrical Machines Lab Eng. Osama Fuad Eng. Nazmi Ashour EXPERIMENT 2 THREE PHASE INDUCTION MOTOR, PART 1 OBJECTIVES To
- Winding 311 and 312 Technical Data Sheet SPECIFICATIONS & OPTIONS STANDARDS Stamford industrial generators meet the requirements of BS EN 60034 and the relevant section of other international standards
ELECTROMAGNETIC INDUCTION Faraday s Law Lenz s Law Generators Transformers Cell Phones Recall Oersted's principle: when a current passes through a straight conductor there will be a circular magnetic field
Aims of this course University of New South Wales School of Electrical Engineering & Telecommunications ELEC4613 - ELECTRIC DRIVE SYSTEMS Course Outline The aim of this course is to equip students with
Faraday s Law INTRODUCTION This experiment examines Faraday s law of electromagnetic induction. The phenomenon involves induced voltages and currents due to changing magnetic fields. (Do not confuse this
ELEN 236 DC Motors 1 DC Motors Pictures source: http://hyperphysics.phy-astr.gsu.edu/hbase/magnetic/mothow.html#c1 1 2 3 Some DC Motor Terms: 1. rotor: The movable part of the DC motor 2. armature: The
Bistable Rotary Solenoid The bistable rotary solenoid changes state with the application of a momentary pulse of electricity, and then remains in the changed state without power applied until a further
INDUCTION MOTORS 1. OBJECTIE To study a 3-phase induction motor, by using its experimentally developed equivalent circuit diagram and by obtaining its basic characteristics: torque/slip, current/slip and
AC motor An AC motor is an electric motor driven by an alternating current. It commonly consists of two basic parts, an outside stationary stator having coils supplied with alternating current to produce