1 Matrix APAX 380V-415V 50Hz TECHNICAL REFERENCE MANUAL FORM: MX-TRM-E REL. September 2014 REV MTE Corporation WARNING High Voltage! Only a qualified electrician can carry out the electrical installation of this filter. Quick Reference Selection Guide Pages 6 10 Installation Guide Pages Startup/Troubleshooting Pages Reference Drawings Pages 24 41
2 TABLE OF CONTENTS 1. WARNINGS...3 WARNINGS AND CAUTIONS... 3 PRODUCT SAFETY LABELING... 3 GENERAL SAFETY INSTRUCTIONS INTRODUCTION...5 RECEIPT & REPAIR STATEMENT HOW TO SELECT...6 SELECTION GUIDE... 6 MODEL NUMBER CODE SYSTEM:... 7 MATRIX APAX VOLTS, 50HZ... 8 FILTER EFFICIENCY, WATT LOSS, CAPACITOR CURRENT PRODUCT SPECIFICATIONS PERFORMANCE SPECIFICATIONS AGENCY APPROVALS WARRANTY TYPICAL PERFORMANCE DATA TYPICAL HARMONIC SPECTRUM MATRIX APAX %LOAD VS POWER FACTOR PERFORMANCE WITH UNBALANCED LINE VOLTAGE (TYPICAL) ALTITUDE DERATING VOLTAGE DISTORTION DERATING CURVE HOW TO INSTALL INSTALLATION CHECKLIST GROUNDING POWER WIRING CONNECTION BASIC SCHEMATIC DIAGRAM INTERCONNECTION DIAGRAM CONTACTOR WIRING OPTION START UP STARTUP CHECKLIST TROUBLESHOOTING HARMONIC FILTER FIELD CHECKS APPENDIX Form: MX-TRM-E September 2014 REV
3 List of Figures Figure 5-1: Typical Harmonic Spectrum with and without Matrix APAX...12 Figure 5-2: Power Factor...12 Figure 5-3: Altitude Derating Curve...13 Figure 5-4: Voltage Distortion Derating Curve...14 Figure 6-1: Basic Schematic Diagram...18 Figure 6-2: Panel Mounted Diagram...19 Figure 6-3: Contactor Wiring Block (44A model shown)...20 List of Tables Table 3-1: Matrix APAX V Panel Mount...8 Table 3-2: Filter Efficiency, Watt Loss, Capacitor Current...9 Table 4-1: Performance Specifications...10 Table 4-2: Over Temperature Switch...11 Table 5-1: Performance with Unbalanced Line Voltage (Typical)...13 Table 8-1: Troubleshooting Guide...23 Form: MX-TRM-E September 2014 REV
4 1. WARNINGS Warnings and Cautions There are two types of warnings in this manual: WARNING Caution WARNING describes situations that can lead to serious faults, physical injuries, or even death. Caution describes situations that can lead to malfunction or possible equipment damage. The following symbols are used in this manual. WARNING WARNING Caution High Voltage Warning: warns of situations that dangerously high voltage is involved. Failure to use proper precautions may lead to serious injury or even death. General Warning: warns of situations that can result in serious injury or death if proper precautions are not used. General Caution: identifies situations that could lead to malfunction or possible equipment damage. Product Safety Labeling The following labels are placed on the Matrix APAX product: Label notes to installer to refer to instruction manual first before installing. High Voltage: surfaces on product can have high voltage which can cause injury. Wait five minutes for capacitors to discharge. Verify safe voltage level before servicing. Connect Thermal Switch: connecting the thermal switch can reduce risk of damage. Form: MX-TRM-E September 2014 REV
5 WARNING WARNING Caution General Safety Instructions High Voltage! Only a qualified electrician can carry out the electrical installation of this filter. High voltage is used in the operation of this filter. Use Extreme caution to avoid contact with high voltage when operating, installing or repairing this filter. Injury or death may result if safety precautions are not observed. The opening of the branch circuit protective device may be an indication that a fault current has been interrupted. To reduce the risk of fire or electrical shock, current-carrying parts and other components of the filter should be examined and replaced if damaged. An upstream disconnect/protection device must be used as required by the National Electrical Code (NEC) or governing authority. Even if the upstream disconnect/protection device is open, the drive down stream of the filter may feedback high voltage to the filter. The drive safety instructions must be followed. Injury or death may result if safety precautions are not observed. The filter must be grounded with a grounding conductor connected to all grounding terminals. Only spare parts obtained from MTE Corporation or an authorized MTE distributor can be used. After removing power, allow at least five minutes to elapse and verify that the capacitors have discharged to a safe level before contacting internal components. Connect a DC voltmeter across the capacitor terminals and ensure that the voltage is at a safe level. Loose or improperly secured connections may damage or degrade filter performance. Visually inspect and secure all electrical connections before power is applied to the filter. Product should not be mounted on wood or any other combustible surface. Doing so could lead to fire or damage to the product. The user of this filter must assure that the input voltage and frequency is correct for the filter rating and that the voltage applied falls within the rated operating tolerance envelop specified for the filter. For sever power line applications where the power feed is likely to experience surges and transients that exceed the input voltage rating, it is recommended that a TVSS (Transient Voltage Surge Suppression) or SPD (Surge Protection Device) be deployed ahead of the filter to reduce the possibility of exceeding the filter rated voltage. Consult with TVSS or SPD manufacturer to determine the correct protection for your power line conditions. Filter must be mounted in the proper orientation per labeling. Fans must be operating properly before powering up the filter. Form: MX-TRM-E September 2014 REV
6 2. INTRODUCTION The purpose of the manual is to properly specify, size, install, interconnect and operate the Matrix APAX filter. For most current information, please refer to website This manual is intended for use by personnel experienced in the operation and maintenance of inverters. Because of the high voltages required by the filter, inverter and the potential dangers presented by rotating machinery, it is essential that all personnel involved in the operation and maintenance of this filter know and practice the necessary safety precautions for this type of equipment. Personnel should read and understand the instructions contained in this manual before installing, operating or servicing the filter and inverter to which it is connected. Receipt & Repair Statement Upon Receipt of this Filter: The Matrix APAX Harmonic Filter has been subjected to demanding factory tests before shipment. Carefully inspect the shipping container for damage that may have occurred in transit. Then unpack the filter and carefully inspect for any signs of damage. Save the shipping container for future transport of the filter. In the event of damage, please contact and file a claim with the freight carrier involved immediately. If the equipment is not going to be put into service upon receipt, cover and store the filter in a clean, dry location. After storage, ensure that the equipment is dry and that no condensation or dirt has accumulated on the internal components of the filter before applying power. Repair/Exchange Procedure MTE Corporation requires a Return Material Authorization Number and form before we can accept any filters that qualify for return or repair. If problems or questions arise during installation, setup, or operation of the filter, please contact MTE for assistance at: Toll Free: MTE ( ) International Tel: Fax: Form: MX-TRM-E September 2014 REV
7 3. HOW TO SELECT Selection Guide The MTE Corporation Matrix APAX Harmonic Filter is designed for harmonic mitigation of 6- pulse inverter drives supplying variable torque loads in a wide variety of applications. The suitability of this filter for a specific application must therefore be determined by the customer. In no event will MTE Corporation assume responsibility or liability for any direct or consequential damages resulting from the use or application of this filter, nor will MTE Corporation assume patent liability with respect to the use of information, circuits or equipment described in this instruction manual. Matrix APAX Harmonic Filters are available in Panel Mount configurations. For inverters feeding isolation transformers select a filter with a current rating equal to or greater than that of the transformer primary current. Please verify information below for proper selection: Line Voltage and Frequency: Input voltage from V, 50Hz. See Table 3-1 (p8) for specification. Current Rating: V, Amp Voltage Distortion: See Figure 5-4 (p14) for voltage distortion derating curve. Contactor Option: Matrix APAX is equipped with user installable contactor options. See Contactor Wiring Option (p20). Temperature: See Table 3-1 (p8) for specification. Altitude: 3,300 feet above sea level without derating. See Figure 5-3 (p13) for derating curve. Enclosure Type: Panel Mounted Form: MX-TRM-E September 2014 REV
8 Model Number Code System: MX P C Matrix APAX Enclosure Type Current Rating P = Panel Mount (No Enclosure) 0006 is 6 Amps 0083 is 83 Amps 0320 is 320 Amps Voltage Frequency Code C Volts 50 Hz Form: MX-TRM-E September 2014 REV
9 Matrix APAX Volts, 50Hz Part Number Selection Tables Panel Mount Filter Amps Rating Part Number Table 3-1: Matrix APAX V Panel Mount App. Wt. (lbs.) App. Wt (kg) Dimensions (in.) (H x W x D) Dimensions (mm) (H x W x D) 6 MXP0006C x 7.4 x x 187 x MXP0008C x 7.4 x x 187 x MXP0011C x 7.4 x x 187 x MXP0014C x 7.4 x x 187 x MXP0021C x 7.6 x x 193 x MXP0027C x 7.6 x x 193 x MXP0034C x 7.6 x x 193 x MXP0044C x 7.6 x x 193 x MXP0052C x 10.6 x x 269 x MXP0066C x 10.6 x x 269 x MXP0083C x 10.6 x x 269 x MXP0103C x 10.6 x x 269 x MXP0128C x 10.6 x x 269 x MXP0165C x 14.8 x x 376 x MXP0208C x 14.8 x x 376 x MXP0240C x 14.8 x x 376 x MXP0320C x 14.8 x x 376 x 396 Ref. Fig. A1 (p25) A2 (p26) A3 (p27) A4 (p28) A5 (p29) A6 (p30) A7 (p31) A8 (p32) A9 (p33) A10 (p34) A11 (p35) A12 (p36) A13 (p37) A14 (p38) A15 (p39) A16 (p40) A17 (p41) Form: MX-TRM-E September 2014 REV
10 Filter Efficiency, Watt loss, Capacitor Current Matrix APAX V, 50Hz Maximum Output Amps RMS Table 3-2: Filter Efficiency, Watt Loss, Capacitor Current Efficiency (Typical) (%) Matrix APAX V, 50Hz V Power Rated Current (Typical) (Watts) Capacitor Current V (Typical) Amps RMS % % % % % % % % % % % % % % % % % Note: Use the IEC AC-3 rating for the corresponding filter capacitor current when selecting a contactor. Form: MX-TRM-E September 2014 REV
11 Total harmonic current distortion* * Typical performance across product range. Service Conditions Input voltage(s) 4. PRODUCT SPECIFICATIONS Performance Specifications Table 4-1: Performance Specifications Maximum output voltage at no load (RMS) +5% Minimum output voltage at full load (RMS) -5% Minimum source impedance 1.5% With DC Link Choke 12% at 40% load 8% at 100% load Without DC Link Choke 17% at 40% load 12% at 100% load Load: 6-pulse variable torque rectifier only VAC +/- 10% Hz. 3 phase Service Factor 1.00 Overload 150% for 1 minute duration with 10% output voltage reduction of nominal of voltage Ambient Temperature (Operating) Open Panel Filters Storage Temperature Altitude Relative Humidity Over Voltage IP Rating Fan Life Expectancy -40 to +50 degrees C -40 to +90 degrees C 0 to 3300 Feet above sea level. Refer to figure 4 for altitude de-rating 0 to 95% non-condensing Category II IP00 80,000 hours at 40C Generator applications: Contactor option is strongly recommended to open capacitors under light load conditions. See section Contactor Wiring Option (p20) for more details. Form: MX-TRM-E September 2014 REV
12 Agency Approvals UL and cul listed to UL508 Type MX and CSA-C22.2 No File E CE Marked Warranty One year from the date of shipment. See for details. Over Temperature Interlock Table 4-2: Over Temperature Switch NC Switch opens at 180 Deg. +/- 5 Deg. C Current Amps Voltage Contact Load AC Resistive Loads AC Inductive Loads AC Resistive Loads AC Inductive Loads 8 12 VDC Resistive Loads 4 24 VDC Resistive Loads MTE stongly recommends the use of the over temperature switch to prevent damage to the filter in rare instances of overheating from abnormal operating conditions. Form: MX-TRM-E September 2014 REV
13 5. Typical Performance Data Typical Harmonic Spectrum Harmonic Current [%} Harmonic Number [n] Drive 100% Load Matrix APAX Filter 100% Load Figure 5-1: Typical Harmonic Spectrum with and without Matrix APAX Matrix APAX %Load vs Power Factor Leading pf Matrix APAX %Load Figure 5-2: Power Factor Form: MX-TRM-E September 2014 REV
14 Performance with Unbalanced Line Voltage (Typical) Table 5-1: Performance with Unbalanced Line Voltage (Typical) All Components at Nominal Values and Worse Case Service Conditions 100% Load Nominal THID 11.39% 1% Unbalance 11.45% 2% Unbalance 11.50% 3% Unbalance 11.66% 30% Load Nominal THID 17.83% 1% Unbalance 17.88% 2% Unbalance 17.92% 3% Unbalance 17.94% Altitude Derating Figure 5-3: Altitude Derating Curve Form: MX-TRM-E September 2014 REV
15 Voltage Distortion Derating Voltage Distortion Derating Curve Derating Factor Voltage Distortion [%] Figure 5-4: Voltage Distortion Derating Curve This plot assists in proper de-rating of a Matrix APAX Harmonic Filter in environments with a preexisting voltage distortion. Example: In a system with 10% voltage distortion, a Matrix filter will need to be oversized by 6% to obtain the same performance as an appropriate filter in a 0% distortion environment. Form: MX-TRM-E September 2014 REV
16 6. HOW TO INSTALL Installation Checklist WARNING Prior to installation, please refer to all general warnings on page 3. Failure to practice this can result in body injury! Input and output wiring to the filter should be performed by authorized personnel in accordance with NEC and all local electrical codes and regulations. The filter is designed for use with copper conductors with a minimum temperature rating of 75 degrees C. Matrix APAX Panel Mount Do not install in or near a corrosive environment. Avoid locations where the filter would be subjected to excessive vibrations. It is recommended that the panel is mounted vertically with the fan at the bottom to allow airflow upwards and away from the reactors. The panel must be located in the lowest temperature regions of the enclosure generally toward the bottom and away from high temperature components. Figures A1 (p25) to A17 (p41) contain outline drawings for the various ratings and show mounting orientation with bolt patterns. Include the power dissipation of the filter along with all the other components located in the enclosure to determine the internal temperature rise and cooling requirements of the enclosure. Allow a minimum of six inches (6 ) around the fan to allow for proper ventilation. Refer to Article 430 Table of the National Electrical code for the selection of the appropriate enclosure Type Number for your application. Form: MX-TRM-E September 2014 REV
17 Grounding WARNING The filter must always be grounded with a grounding conductor connected to ground terminals. Cable Shield Grounding For cable shield grounding follow the drive manufactures recommendations. Over Temperature Interlock An over temperature interlock circuit should be used in conjunction with thermal switch to turn off the drive to prevent filter damage due to abnormal operating conditions. The temperature switch is normally closed and will open when an internal reactor temperature of 180 C is reached. See Figure 6-1 (p18) or Figure 6-2 (p19) for wiring information and the drive user manual for interconnection information. Form: MX-TRM-E September 2014 REV
18 WARNING Power Wiring Connection Input and output power wiring to the filter should be performed by authorized personnel in accordance with the NEC and all local electrical codes and regulations. Cable lugs and mounting hardware are provided by the customer. Any extremely low or high resistance readings indicate a mis-wire and may result in damage to filter components if not corrected. Verify that the power source to which the filter is to be connected is in agreement with the nameplate data on the filter. A fused disconnect switch or circuit breaker should be installed between the filter and its source of power in accordance with the requirements of the NEC and all local electrical codes and regulations. Refer to the drive user manual for selection of the correct fuse rating and class. The filter is designed for use with copper conductors with a minimum temperature rating of 75 degrees C. Refer to the drive user manual for instructions on interconnecting the drive and motor and the correct start-up procedures for the drive. Wiring Checks Using Figure 6-1: Basic Schematic Diagram (p18), visually check the wired components to confirm, verify, and correct wiring. Then, with a multi meter check phase to phase isolation using the 100K ohm range. The multi meter will read the parallel equivalent of the bleeder resistors after the capacitors initially charge. All phase to phase resistance values should be the same. Check for the Following Faults: Capacitor shorted Capacitor bus not connected Capacitor bus to chassis short Paralleling wiring errors Grounding and Ground Fault Protection The filter must always be grounded with a grounding conductor connected to all ground terminals. Due to high leakage currents associated with variable frequency drives, ground fault protective devices do not necessarily operate correctly when placed ahead of a Matrix Filter feeding a drive. When using this type of device, its function should be tested in the actual installation. Form: MX-TRM-E September 2014 REV
21 Contactor Wiring Option The Matrix APAX comes with a user configurable contactor wiring block. This option allows the user to add disconnect options to meet their applications. Figure 6-3 (p20) shows a representation of the contactor wiring block (the terminal block varies depending on model size). Refer to Figure 6-2 (p19) for the wiring diagram. The units will be shipped with factory installed jumpers as shown in the figure. Jumpers must be removed for installation of contactor option. Figure 6-3: Contactor Wiring Block (44A model shown) Form: MX-TRM-E September 2014 REV
22 7. START UP Startup Checklist Safety Precautions Before startup, observe the following warnings and instructions: WARNING Internal components of the filter are at line potential when the filter is connected to the drive. This voltage is extremely dangerous and may cause death or severe injury if you come in contact with it. Use extreme caution to avoid contact with line voltage when checking for power. INJURY OR DEATH MAY RESULT IF SAFETY PRECAUTIONS ARE NOT OBSERVED. Damage to equipment or serious injury may occur if the inverter startup procedures are not observed. Sequence of Operation 1. Read and follow safety precautions. 2. For units with fans, install the unit so that fans are at the bottom to allow airflow upwards over the reactors. 3. After installation, ensure that: a. All filter ground terminals are connected to ground. b. Power wiring to the utility, drive and motor is in accordance with the power wiring connection diagrams shown in installation instructions section. 4. Check that moisture has not condensed on the filter components. If moisture is present, do not proceed with startup until the moisture has been removed. 5. Disconnect the filter output from the drive. 6. Connect the filter to the utility. 7. Confirm that line voltage is present at the input terminals (U, V1, W1) of the filter. 8. Confirm that line voltage is present at the output terminals (U2, V2, W2) of the filter and that it is less than or equal to 1.05 times the input voltage. 9. Verify that the fans are operational on units that are equipped with fans. 10. Ensure that the thermal switch is connected. 11. Using a clamp on Amp meter, check input phase currents to verify they are within a 5% match to each other and approximately 30% of filter current rating. 12. Remove power and verify that NO VOLTAGE is present on the filter terminals. 13. Connect the filter output to the drive. 14. Refer to the drive user manual for the drive startup procedure. Observe all safety instructions in the drive user manual. Form: MX-TRM-E September 2014 REV
23 8. TROUBLESHOOTING WARNING INJURY OR DEATH MAY RESULT IF THE DRIVE SAFETY PRECAUTIONS ARE NOT OBSERVED. When properly installed, this equipment has been designed to provide maximum safety for operating personnel. However, hazardous voltages and elevated temperatures exist within the confines of the enclosure. Servicing should therefore be performed by qualified personnel only and in accordance with OSHA Regulations. High voltage is used in the operation of this filter. Use Extreme caution to avoid contact with high voltage when operating, installing or repairing this filter. INJURY OR DEATH MAY RESULT IF SAFETY PRECAUTIONS ARE NOT OBSERVED. Please refer to Figure 6-1: Basic Schematic Diagram (p18) and Figure 6-2: Panel Mounted Diagram (p19) to aid in troubleshooting. Harmonic Filter Field Checks 1. Read and understand the voltage appropriate MTE Matrix Filter user manual. These manuals may be downloaded from the web site. Locate figures and drawings for your particular filter and identify the terminal locations. 2. Disconnect all power and remove input power wiring from U1, V1, W1 terminals. 3. Remove VFD drive power connections from filter terminals U2, V2, W2 and any contactor or temperature switch wiring. (For filters using control transformers: remove power fuses on top of transformer.) 4. Visually inspect filter terminals and wiring lugs for signs of heat and corrosion. Contact factory if any wires appear to be missing or cut! 5. Inspect the U4, V4, W4 capacitor interconnect terminals and wiring. 6. Visually inspect all capacitors for signs of case deformation, bowing of the top or terminal damage. Note the CAP- # and date code of any damaged capacitors. 7. Using a multi meter set to read 100K ohms check: a. Phase to phase U1-V1-W1-U1 (mechanically activate contactor if present) after reactor and caps charge reading should be about 40K (total equivalent breeder resistance value) and should be the same for each phase. Open circuit or very low readings indicate a problem. b. Phase to chassis U1- case, V1-case, W1- case; low readings indicate a ground fault problem. 8. Ensure the disconnect is safe, then wire the utility power to U1, V1, W1. 9. Apply power and verify that proper output voltage is present on U2, V2, and W Using a clamp on amp meter read the filter input current: a. Readings will be 0.4 of the capacitor current listed in Table 3-2: Filter Efficiency, Watt Loss, Capacitor Current (p9), for the listed filter current in the user manual (mechanically activate the contactor if the filter is equipped with one). Readings Form: MX-TRM-E September 2014 REV
24 should be the same (+/- 5%) for all phase currents; contact the factory if currents are out of tolerance! b. Open contactor readings will show zero current for all phases. 11. Disconnect filter power and wire the VFD to U2, V2, and W2 as well as any control wiring to the filter contactor or temperature switch. Replace any control transformer fuses. Follow the drive power startup guidelines in the drive manufacturer s user manual. Table 8-1: Troubleshooting Guide PROBLEM: Line voltage is not present at the filter output terminals. Possible cause: Power to the filter is turned off. Solution: Turn power on. Possible cause: One or more external line fuses are blown. Solution: Verify the continuity of line fuses in all phases. Replace as necessary. PROBLEM: Full Load Harmonic current distortion exceeds 15% on one or more phases at full load. Possible cause: A capacitor has failed. Solution: Inspect the tops of all capacitors for bowing. Replace failed capacitors. Possible cause: Source impedance is less than 1.5%. Solution: Add a minimum 1.5% impedance line reactor to the filter input. Possible cause: Input source voltage harmonic distortion. Solution: Identify equipment causing harmonic voltage distortion and add filters as required or accept elevated THVD. PROBLEM: Filter output voltage is not within specification Possible cause: Filter input voltage is not within specification. Check the AC input line voltage and verify that it is within tolerance. Refer Solution: to the filter service conditions and performance specifications for tolerances. Possible cause: Source impedance is out of tolerance. Solution: Verify that the source impedance is within tolerance. Refer to the filter service conditions and performance specifications for tolerances. Possible cause: One or more Capacitors is damaged. Solution: Visually check capacitor top for distortion or doming. Check for shorts or open caps. Replace failed capacitors. Possible cause: Drive set up parameter does not allow for input filter Solution: Consult drive manufacturer to update setup to accommodate input filter. Possible cause: Input voltage subject to extreme transients such as switching between two voltage sources. Drive faults on over or under voltage. Source switching is not recommended without proper phase Solution: synchronizing or allowing reasonable time delay before transfer to new source. Form: MX-TRM-E September 2014 REV
25 APPENDIX Reference Drawings Form: MX-TRM-E September 2014 REV
26 Figure A1: MXP0006C Form: MX-TRM-E September 2014 REV
27 Figure A2: MXP0008C Form: MX-TRM-E September 2014 REV
28 Figure A3: MXP0011C Form: MX-TRM-E September 2014 REV
MATRIX FILTER SERIES D 600 Volts, 60HZ USER MANUAL PART NO. INSTR 026 REL. 120628 REV. 007 2012 MTE Corporation Matrix Series D User s Manual 600VAC IMPORTANT USER INFORMATION NOTICE The MTE Corporation
M T E C o r p o r a t i o n MTE Series RL Line/ load Reactors USER MANUAL PART NO. INSTR -011 REL. 050516 2002 MTE Corporation IMPORTANT USER INFORMATION NOTICE MTE Series RL Line/Load Reactors are components
M T E C o r p o r a t i o n MTE Series RL Line/ load Reactors USER MANUAL PART NO. INSTR -011 REL. 060227 2006 MTE Corporation Important User Information NOTICE MTE Series RL Line/Load Reactors are components
PowerOhm Installation Manual for LG ATV Series Braking Modules IMPORTANT: These instructions should be read thoroughly before installation. All warnings and precautions should be observed for both personal
HarmonicGuard Series Drive-Applied Harmonic Filter Installation, Operation, and Maintenance Manual No part of this publication may be reproduced, stored in a retrieval system, or transmitted in any form
Table of Contents TABLE OF CONTENTS...1 STANDARD DELIVERY SCHEDULE...2 REACTOR SELECTION & PRICING...4 208-240 VOLT (3-PHASE)...4 400 VOLT (50 HZ) USE FOR 380-415 VOLTS...5 480 VOLT (3-PHASE) REACTOR...6
Hitachi America, Ltd. RCU Series Regenerative Converter Unit Instruction Manual NOTE: REFER ALSO TO APPLICABLE INVERTER INSTRUCTION MANUAL Manual Number: HAL1057A May 2010 After reading this manual, keep
PART 0 DESIGN STANDARDS 0.01 GENERAL DESIGN GUIDELINES A. Coordinate starter needs for mechanical equipment prior to 50% CD and confirm again for 100% CD submittal. B. Coordinate temperature controls requirements
SECTION 26 28 16 ENCLOSED SWITCHES AND PART 1 - GENERAL 1.1 SUMMARY A. Section includes the following individually mounted, enclosed switches and circuit breakers rated 600V AC and less: 1. Fusible switches.
A6Z OPERATING MANUAL TABLE OF CONTENTS Introduction... p. 2 Features... p. 2 Description... p. 3 Theory of Operation... p. 3 Installation... p. 4 Electrical Connections... p. 5 Options... p. 6 Warranty.p.
KLR Series Three Phase Reactors PRODUCT SPECIFICATIONS Lifetime Warranty Performance Guarantee K-Rated, UL/ULC-Recognized; CSA-Certified 3 Phase, 600V Class Gapped Iron Core Inductor All Copper Windings
Supersedes: 160.75-PW2 (508) Form 160.75-PW2 (311) FIELD CONNECTIONS FOR YK CHILLER (STYLE G) OPTIVIEW CONTROL CENTER WITH REMOTE MEDIUM VOLTAGE SSS WIRING DIAGRAM CONTRACTOR ORDER NO. YORK CONTRACT NO.
PHASE PERFECT PHASE CONVERTERS OPERATION & INSTALLATION MANUAL PHASE TECHNOLOGIES, LLC 1 DANGER: HIGH VOLTAGE Electric shock could result in death or injury. qualified personnel for installation. Please
A3Z OPERATING MANUAL TABLE OF CONTENTS Introduction... p. 2 Features... p. 2 Description... p. 3 Theory of Operation... p. 3 Installation... p. 4 Electrical Connections... p. 5 Options... p. 6 Warranty...
PM500 Voltage Regulator User Manual A Regal Brand Scan here for other languages. Introduction The PM500 is an encapsulated electronic voltage regulator intended for use with Marathon Generators PMG system.
Technical Manual DLM Module This manual should remain with the unit. Safety Rules SAVE THESE INSTRUCTIONS! Read the following information carefully before attempting to install, operate or service this
A1P OPERATING MANUAL TABLE OF CONTENTS Introduction... p. 2 Features... p. 2 Description... p. 3 Theory of Operation... p. 3 Installation... p. 4 Electrical Connections... p. 5 Options... p. 6 Warranty...
INSTRUCTION MANUAL FOR VOLTAGE REGULATOR APR 125-5 P/N 9168800100 Publication: 9168800990 Revision: J 03/09 INTRODUCTION This instruction manual provides information about the operation and installation
User s Manual ACS550-CC Packaged Drive with Bypass Supplement for ACS550-01/U1 Drives User s Manual ii ACS550-CC Packaged Drive with Bypass ACS550 Drive Manuals GENERAL MANUALS ACS550-01/U1 Drives User's
User s Manual ACH550-CC/CD Packaged Drive with Classic Bypass Supplement for ACH550-UH HVAC User s Manual ii ACH550-CC/CD Packaged Drive with Classic Bypass ACH550 Drive Manuals GENERAL MANUALS ACH550-UH
Illuminator Series CM GUIDE SPECIFICATIONS And TECHNICAL DESCRIPTION 500W, 1000W, 1500W and 2000W Single-Phase Emergency Power System This description contains all the necessary functional and technical
INSPECTOR LINE LOAD SIMULATOR INSTRUCTION MANUAL INS120P TASCO, INC. THIS TESTER IS DESIGNED FOR USE ONLY BY QUALIFIED ELECTRICIANS. IMPORTANT SAFETY WARNINGS mwarning Read and understand this material
SPECIFICATIONS AIR COOLED RECTIFIER Spec50a1 5JAN1999 SPECIFICATION S-50-A HIGH VOLTAGE SINGLE TRANSFORMER AIR COOLED RECTIFIER Standard output power range: 250 to 600 volts at 100 to 1,200 amperes TECHNICAL
User s Manual ACS550-CC Packaged Drive with Bypass Supplement for ACS550-01/U1 Drives User s Manual ii ACS550-CC Packaged Drive with Bypass ACS550 Drive Manuals GENERAL MANUALS ACS550-01/U1 Drives User's
The Z Series Zero-Fired SCR Power Controllers 60-1200 AMPS 120-600 VAC SCR Power controllers for resistance heating applications. ROBICON 1996 Rev. 7/96 Applications Robicon s Z series power controls are
MODEL 422 Submersible Pump Controller Monitors True Motor Power (volts x current x power factor) Detects Motor Overload or Underload Operates on 120 or 240VAC, Single-phase or 3-phase Built-in Trip and
SCR Power Controllers Instruction Manual SCR POWER CONTROLLERS TABLE OF CONTENTS General Description and Specifications...1 Firing Modes....2 Installation and Wiring...4 Operation...9 Troubleshooting...15
Application Engineering March 2011 Copeland Digital Compressor Controller Introduction The Digital Compressor Controller is the electronics interface between the Copeland Scroll Digital compressor or the
GP/GPA GROUND FAULT PROTECTION GROUND FAULT PROTECTION C-220EM Instruction Manual, June 2015 ABOUT I-GARD I-Gard s commitment to electrical safety provides both industrial and commercial customers with
Vari Speed A2000 TABLE OF CONTENTS Control Features Options Application Data Operating Condition s Control Ratings Chart Mounting Dimensions Installation and Wiring Typical Wiring Diagram Schematic (Block
Specification sheet OTEC Transfer switch open transition 40 1200 amp Description OTEC transfer switches are designed for operation and switching of electrical loads between primary power and Standby generator
Sola/Hevi-Duty S3K Series Mini-Tower UPS GUIDE SPECIFICATIONS 700VA to 1600VA 120V models Single - Phase Uninterruptible Power Supply Systems 1.1 SUMMARY 1.0 GENERAL This specification defines the electrical
About Power System Solutions mission The Power System Solutions Mission Statement To achieve customer satisfaction by providing innovative solutions to improve upon power quality, energy efficiency, and
Table of contents 1 Introduction... 2 1.1 General... 3 1.2 Theory of Operation... 3 1.3 Brake Sizing and Selection... 3 1.4 Applications... 5 1.5 Where Mechanical Brakes Should be Used... 5 1.6 ABC Model
Instructions for Installation and Operation Filtered PWM Speed Control for Permanent Magnet DC Motors Model 0794 Speed and Direction Control up to 5/8 HP NEMA-1/IP-20 Specifications Product Type:... WPM-2148E1
Go Power! Manual GP-1000 Inverter Go Power! Electric Inc. PO Box 6033 Victoria, BC V8P 5L4 Tel: 866-247-6527 Fax: 866-607-6527 Email: email@example.com Table of Contents 1. INTRODUCTION 3 2. SPECIFICATIONS
Installation Instructions Ecosine evo IP21 cover kits Ecosine evo FN 3440 / FN 3441 (50 Hz) for 380 415 V AC FN 3450 / FN 3451 (50 Hz) for 440 500 V AC FN 3452 / FN 3453 (60 Hz) for 440 480 V AC Schaffner
Dual-Lite Trident TRF 40 Wide Battery Cabinet 20-40kVA Systems USER MANUAL 755-00020-DL 5/17/2017 2 755-00020-OEM R01 TABLE OF CONTENTS 1. Important Information About This Manual... 4 1.1 Manual Symbols...
1-800-443-4859 8300 Series Installation Guidelines WARNING: RISK OF ELECTRICAL SHOCK OR BURNS. THIS CONVERTER ASSEMBLY SHOULD BE INSTALLED BY A QUALIFIED ELECTRICIAN OR CERTIFIED RV TECHNICIAN. IMPROPER
Go Power! Manual GP-1750HD Inverter GP-2500 Inverter Go Power! Electric Inc. PO Box 6033 Victoria, BC V8P 5L4 Tel: 866-247-6527 Fax: 866-607-6527 Email: firstname.lastname@example.org Table of Contents 1. INTRODUCTION...
MORATTO S.R.L. Electrical Machinery I 31030 PERO DI BREDA (Treviso) Italy Via A Volta, 2 Tel. +390422904032 fax +39042290363 www. moratto.it - email@example.com THREE PHASE AND SINGLE PHASE ASYNCHRONOUS
MAKING MODERN LIVING POSSIBLE Quick Setup VLT FCM 300 Series Factory setting Motors type B14 & B34 mounting Reset (pushbutton) Start Jog Speed reference Fig. 1 - Reset to be closed short time for resetting
ESD5500E Series Speed Control Unit 1 SPECIFICATIONS INTRODUCTION PERFORMANCE Isochronous Operation ± 0.25% or better Speed Range / Governor 1-7.5 KHz Continuous Speed Drift with Temperature ±1% Maximum
Issue 5 24/48 VOLT DC SWITCHING POWER SUPPLY INTRODUCTION These instructions provide the specifications, installation and maintenance information for the VP-4124 and VP-4124-E, 24/48 Volt Power Supplies.
Technical Note 10406 XLM Energy Storage Module XLM 62V Energy Storage Module Introduction The XLM energy storage modules are self-contained energy storage devices comprised of twenty-three individual supercapacitor
This fuse technology guide will discuss basic fuse operating, application, and selection criteria concepts. The intended purpose of this section is to aid designers with the operation and characteristics
NetSure 701 Series DC Power System DC Power for Business-Critical Continuity Key Features n n High Efficiency approaching 97%, esure rectifiers reduce power consumption for lower operating costs Modular
Electric Motor Controls BOMA Pre-Quiz Name: 1. How does a U.P.S. (uninterruptable power supply) work? A. AC rectified to DC batteries then inverted to AC B. Batteries generate DC power C. Generator, batteries,
Återförsäljare: Tre Röda AB TillingeHagby 7-745 94 ENKÖPING Tel: 08-560 200 22 e-post: firstname.lastname@example.org http: www.treroda.nu When the INSIDE is important make the OUTSIDE Cannon TECHNICAL DATA SHEET 400-500-600-800
INDUSTRIAL POWER SUPPLIES SFL-SERIES Operating Instructions 1. Application The SFL-series are compact, rugged switching power supplies designed for applications in process automation and other industrial
1-800-443-4859 5300 Series Installation Guidelines WARNING: RISK OF ELECTRICAL SHOCK OR BURNS. THIS CONVERTER ASSEMBLY SHOULD BE INSTALLED BY A QUALIFIED ELECTRICIAN OR CERTIFIED RV TECHNICIAN. IMPROPER
World Class Power Solutions Rectifiers For Stationary Battery Systems in Nuclear Power Plants General 2 1.1 Application Electronically controlled rectifier assemblies are used in conjunction with suitable
QS Rule Raritan PX Power Cord Installation Guide This installation guide explains how to install power cords on Raritan PX products that do not come with a factory installed power cord. This type of product,
LEESON ELECTRIC MOTORS, GEARMOTORS AND DRIVES R User s Manual 17429X.00 SERIES MODELS: 174298.00 174299.00 PWM REGENERATIVE DC TO DC DRIVES II Table of Contents 17429X.00 Drives...............................................................
TECHNICAL DATA SHEET INFINITY 3300 10 15 20 kva 3Ph(in) 3Ph(out) GENERAL INFORMATION POWER - kva 10 15 20 UPS typology ON LINE Double conversion ACTIVE stand by-operation (Optional) Nominal output power
SECTION 230513 - MOTORS AND ADJUSTABLE SPEED DRIVES PART 1 - GENERAL 1.1 DESCRIPTION A. Provide labor, materials, equipment and services as required for the complete installation designed in Contract Documents.
READ AND FOLLOW ALL SAFETY INSTRUCTIONS! SAVE THESE INSTRUCTIONS AND DELIVER TO OWNER AFTER INSTALLATION IMPORTANT SAFEGUARDS! When using electrical equipment, basic safety precautions should always be
SDS Enclosed Star-Delta Starter User Guide (7.5kW~90kW) V2.0.0 PLEASE NOTE: AS STANDARD AND UNLESS OTHERWISE SPECIFIED, THIS PRODUCT IS EQUIPPED WITH A BASIC LOW INTEGRITY EMERGENCY STOP CIRCUIT STOPPING
PS-1X Series Power Supply Unit Information & User Manual AC to DC Power Supply Unit for Motion Control Applications Model No s: PS-1X0 and PS-1X2 Ultra Motion PSU Manual 1 Safety Information IMPORTANT:
CN100A110 SERIES Instruction Manual BEFORE USING THE POWER SUPPLY UNIT Be sure to read this instruction manual thoroughly before using this product. Pay attention to all cautions and warnings before using
ALTIVAR FLEX58 Chassis Drive Controller Product Selection Class 8806 CONTENTS Description Page General Information and Selection....................................... 2 Specifications and Ratings...........................................
TC2000 TC2001 EUROTHERM ONTROLS Two phase thyristor power switches Product data TC2000 TC2001 Thyristor power switches Compact, two phase thyristor power switches for electrical heating applications from
PART 1 - GENERAL 1.1 GENERAL: SECTION 15150 MOTORS, MOTOR STARTERS, VARIABLE FREQUENCY DRIVES AND ELECTRICAL WORK A. The Mechanical Contractor shall furnish to the Electrical Contractor for installation,
Cougar B Series Electric Vibrators 3 Frame Go to Cougar B Series Electric Vibrators web page Operator s Manual M3929 Important MARTIN ENGINEERING HEREBY DISCLAIMS ANY LIABILITY FOR: DAMAGE DUE TO CONTAMINATION
SOLAR LIGHTING CONTROLLER OPERATOR S MANUAL SUNLIGHT MODELS INCLUDED IN THIS MANUAL SL-10 SL-10-24V SL-20 SL-20-24V 10A / 12V 10A / 24V 20A / 12V 20A / 24V 1098 Washington Crossing Road Washington Crossing,
PT Series Phase Converters OPERATION & INSTALLATION MANUAL SAFETY MESSAGES AND WARNINGS To ensure safe and reliable operation of the PT Series phase converter, it is important to carefully read this manual,
41-348.1H Type SA-1 2.1. RESTRAINT CIRCUIT The restraint circuit of each phase consists of a center-tapped transformer, a resistor, and a full wave rectifier bridge. The outputs of all the rectifiers are
HPV 100 Hydraulic Elevator Soft-Starter Technical Manual WARRANTY Standard products manufactured by the Company are warranted to be free from defects in workmanship and material for a period of one year